... 



(Stamp comment
#41 dborgstadt
12/19/2010 12:51:55 PM
blank)
SIZE I DWGNO I SH 
1 I R~ IA 377A4380 + THIRD ANGLE PROJECTION REVISIONS .e REV DESCRIPTION DATE APPROVED 
APPROVED FOR CONSTRUCTIDN 01-07-26 RG 
DAVIl HMATTICE RS 
A APPROVED FOR CONSTRUCTIDN 02-02-26 RG 
ADDED CABLES: C235C, C85, C414A, C421, C421A,B,C, C422, RS 
THIS DOCUMENT SHALL BE C422A, C426A, C549, C549A, C610F,FA,FB,FC,HHA,J,V,W, C611A, 
REVISED IN ITS ENTIRETY, ALL 
C615D, C776, cm. 
DELETED CABLES: C124, C405, C412, C417B, C418B, C419A,B, 
SHEETS OF THIS DOCUMENT C427, C551D, C615C, C616A,B,C. 
ARE THE SAME REVISION LEVEL REVr.3ED CABLES: C237, C426, C591, C593, C610B,C,D,E, C819. 
JAMES WHITESCARVER 
AS INDICATED IN THE REVISION B APPROVED FOR CONSTRUCTIDN 02-04-22 RG 
BLOCK. REVISED LEVEL AND PURPOSE ON C874 RS 
DC101037294 
JAMES WHITESCARVER 
C APPROVED FOR CONSTRUCTIDN 021213 RG 
REVISED PER DCI 020191121 020023068 RS 
ADDED CABLES: C480,C481 
REVISED PURPOSE OF CABLE: C149 
RAVi'lDRAN DEVARAJAN 
CABLE SUMMARY (GAS TURBINE) 
PROJECT: PSEG MORRISTOWN 
MADE FOR: PSEG POWER LLC 
PPE PROJECT NO.: 512M1071 
©COPYRIGHT 2DJ2 GENEr:;PL ELECTRIC COMPPNY 
PROPRIETAAY Ir~FORMATlor~ -THIS DOWMENT co~TPJNS IGASTURB OM GR0730 
IPROPRIETPRY IrJFORMATlor~ OF GENERAL ELECTRIC GASTURB ML 7A1PEA234-1 T 4 
COMPANY AND MAY NJT BE USED OR DGCLOSED TO 
OTHERS, EXCEPT WIT-1 THE WRITIEN PERMISSION Cf 
GE~JERPL ELECTRIC COMPANY 
liNt FSS OTHFRWISF SPFOFIFn SIGNATIIRFS nATF r:FNFRAJ FI F(;TRlr, r,m..P!'INY 
DIMENSIONS PRE IN I\JCHES 0,""" 01-07-26 GE Power GenerationTCLERM~CES ON DAVID H MATTICE ~ 
2 PL DECIMPLS ~ CHECK_D 
DAVID H MATTICE 
01-07-26 SCHENECTADY, NY 
:1 PI nF(:IMAI S~ ENGRG 
ROBERT GARNER 
01-07-26 CABLE SUMMARY 
MGLES~ ISSUEC 
BONNIE A ROSBOZOM 
01-07-26 
FF:ACTIQ\JS ~ " FRST MADE FOR 512M1071 PPE MDL 0463 
SIZE CAGE CODE DWGNO 
A 377A4380 
SIMTO: SCALE NONE I I SHEET 1of 30 
+ 

.. 



(Stamp comment
#41 dborgstadt
12/19/2010 12:56:35 PM
blank)
I~ IREVC I + 
NOTES 
1 "C" PREFIX INDICATES CABLE SUPPLIED BY OTHERS THAN GEGAS 
TURBINE DIVISION. CONTROL CABLES WITH "C" PREFIX 
CONTAIN A NOMINAL NUMBER OF SPARES. 
2 "C" PREFIX CABLES TO BE RATED NOT LESS THAN 90 DEG. C. 
3 CABLE GLANDS/STRESS RELIEFS FOR CONNECTING CABLES AT 
JUNCTION BOXES/DEVICES ARE TO BE SUPPLIED BY OTHERS. 
4 BEND RADIUS -ALL BENDS SHALL BE SO MADE THAT THE CABLE 
WILL NOT BE DAMAGED, AND THE RADIUS OF THE INNER EDGE OF 
ANY BEND SHALL NOT BE LESS THAN SHOWN IN TABLE. THIS 
RADIUS DOES NOT INCLUDE PULLING TENSION CALCULATION. 
SEE M.L. ITEM 0435 FOR FURTHER DEFINITION. 
5 CABLES SUPPLIED BY OTHERS THAT ARE SHOWN ON THIS DWG. 
ARE ONLY FOR THOSE WHICH INTERFACE WITH GAS TURBINE 
SUPPLIED EQUIPMENT. 
6 MAKEUP OF "C' PREFIX CABLES ARE SUGGESTED TO ENSURE 
SUFFICIENT CONDUCTOR COUNT. 
7 "C" PREFIX CABLES FOR LEVEL 4 AND LEVEL 5 POWER SUPPLY 
ARE SIZED BY OTHERS. 
8 SEE OUTLINE, GAS TURBINE PACKAGE CONNECTION ELECTRICAL 
DIAG., M.L. ITEM 0301 FOR LOCATION OF CABLE 
DESTINATION POINTS (JB'S, ETC.) WITHIN EACH ON-BASE 
COMPARTMENT. 
9 CABLE TO BE INSTALLED WITH ADEQUATE SEPARATION 
BETWEEN DIFFERENT LEVELS AND IN PROPER CONDUIT OR 
RACEWAY MATERIAL, SEE M.L. ITEM 0435, AND IN ACCORDANCE 
WITH LATEST ELECTRICAL CODES. 
10 GROUND CABLES ARE TO BE SUPPLIED ON ALL EQUIPMENT. TWO 
CABLE CONNECTIONS ARE DIAGONALLY OPPOSED. 
11 ONE CABLE REQUIRED PER SITE. 
12 CABLE REQUIRED FOR UNITS 1 & 3 ONLY. 
13 CABLE REQUIRED FOR UNITS 2 & 4 ONLY. 
14 FOR ADDITIONAL COMMUNICATION CABLES SEE M.L. ITEM 4108. 
15 REFER TO DWG. 358B1001 FOR CABLE ROUTING. 
GENERAL ELECTRIC COMPANY•~~=G=E==p=O=~=e=r=G__e_n_e_ra_t_io__n ________ ~
DRAWN 
DAVID H MATTICE 01-07-26 
SIZE 
~ 
CAGE CODE DWGNO 
377A4380 
ISSUED DOCUMENT SERVICES 01-07-26 SCALE NONEI I SHEET 2

+ (GR0730) 


.. 


I~ IREVC I + 
LOCATION DESCRIPTIONS 
001 -WELDING RECEPTACLE ONE 
101 -TURBINE CONTROL PANEL (333) 
102 -GENERATOR CONTROL PANEL (333) 
108 -AUXILIARY RELAY PANEL 
114 -JB001 ACCESSORY BASE LOW LEVEL (119) 
115-JB002 ACCESSORY BASE LEVEL3(119) 
118 -ACCESSORY BASE MOTORS (119) 
119 -ACCESSORY BASE 
114 -JB001 ACCESSORY BASE LOW LEVEL 
115 -JB002 ACCESSORY BASE LEVEL 3 
118 -ACCESSORY BASE MOTORS 
149 -CRANKING MOTOR 
348 -JB077A ACCESSORY BASE FP 
392 -JB004 ACCESSORY BASE LEVEL 4 
121 -TURBINE BASE 
122 -TURBINE ROOF MOUNTED DEVICES 
125 -JB055 TURBINE BASE LOW LEVEL 
126 -JB056 TURBINE BASE LOW LEVEL 
390 -JB034 TURBINE ROOF LOW LEVEL 
122 -TURBINE ROOF MOUNTED DEVICES (121) 
125 -JB055 TURBINE BASE LOW LEVEL (121) 
126 -JB056 TURBINE BASE LOW LEVEL (121) 
127 -JB085 LOAD GEAR COMPARTMENT LOW LEVEL (250) 
128 -EXHAUST FRAME BLOWER 88TK-1 
129 -EXHAUST FRAME BLOWER 88TK-2 
133 -JB005C GENERATOR COMPARTMENT LEVEL 4 (134) 
134 -GENERATOR COMPARTMENT 
133 -JB005C GENERATOR COMPARTMENT LEVEL 4 
135 -JB005A GENERATOR COMPARTMENT LOW LEVEL 
136 -JB005B GENERATOR COMPARTMENT LEVEL 3 
325 -JB163 GENERATOR COMPARTMENT LOW LEVEL 
135 -JB005A GENERATOR COMPARTMENT LOW LEVEL (134) 
136 -JB005B GENERATOR COMPARTMENT LEVEL 3 (134) 
146 -METAL CLAD SWITCHGEAR 
149 -CRANKING MOTOR (119) 
151 -JB215 GENERATOR FILTER SEQUENCER 
156 -FUEL GAS FLOW DEVICES 
157 -TURBINE AIR INLET FILTER COMPARTMENT 
449 -JB078 TURB. AIR INLET FILTER COMPARTMENT 
158 -GAS SCRUBBER 
563 -JB386 GAS SCRUBBER LEVEL 3 
161 -COOLING WATER MODULE #1 
428 -JB090 COOLING WATER MODULE LEVEL 3 
438 -JB090A COOLING WATER MODULE LEVEL 4 
171 -GAS FUEL (VALVE) MODULE 
363 -JB130 GAS FUEL MODULE 
441-JB131 GAS FUEL MODULE LEVEL4 
172 -AIR PROCESS SKID 
455 -JB297 AIR PROCESS SKID LEVEL 3 
176 -LUBE OIL DEMISTER (TURBINE) 
182 -MAIN TRANSFORMER (STEP UP) 
183 -AUXILIARY POWER TRANSFORMER 
(Stamp comment
#41 dborgstadt
12/19/2010 12:56:31 PM
blank)
GENERAL ELECTRIC COMPANY•~~=G=E==p=O=~=e=r=G__e_n_e_ra_t_io__n ________ ~
DRAWN 
DAVID H MATTICE 01-07-26 
SIZE 
~ 
CAGE CODE DWGNO 
377A4380 
ISSUED DOCUMENT SERVICES 01-07-26 SCALE NONEI I SHEET 3

+ (GR0730) 


.. 



(Stamp comment
#41 dborgstadt
12/19/2010 12:56:28 PM
blank)
14' IREvc I 
LOCATION DESCRIPTIONS (continued) 
201 -LIMIT AMP 
208 -VIBRATION MONITOR PANEL (102) (333) 
225 -RELATIVE HUMIDITY SENSOR 
227 -HAZARDOUS GAS MONITOR (102) (333) 
230 -JB019A TURBINE OFF BASE RACK LEVEL 3 
+ 
231 -JB019B TURBINE OFF BASE RACK LEVEL 3 
233 -JB020A TURBINE OFF BASE RACK LOW LEVEL 
234 -JB020B TURBINE OFF BASE RACK LOW LEVEL 
250 -LOAD GEAR COMPARTMENT 
127 -JB085 LOAD GEAR COMPARTMENT LOW LEVEL 
387 -JB020G TURBINE COMPARTMENT LOW LEVEL 
252 -WATER WASH SKID 
456-JB010 WATERWASHSKID LEVEL3 
254 -CUSTOMER DEVICES--PANELS 
257 -JB037 PERFORMANCE MONITORING LOW LEVEL 
280 -GENERATOR NEUTRAL ACCESSORY COMPARTMENT GNAC 
581 -JB005N GEN. NEUTRAL ACCESSORIES COMPo LEVEL 3 
283 -FIRE PROTECTION DEVICES 
284 -FIRE PROTECTION PANEL 
325 -JB163 GENERATOR COMPARTMENT LOW LEVEL (134) 
329 -CRANKING MOTOR TRANSFORMER 
333 -PACKAGED ELECTRICAL-ELECTRONIC CONTROL CENTER-PEECC 
101 -TURBINE CONTROL PANEL 
102 -GENERATOR CONTROL PANEL 
208 -VIBRATION MONITOR PANEL 
227 -HAZARDOUS GAS MONITOR 
334 -PEECC MOTOR CONTROL CENTER 
339 -JB298 PEECC LEVEL 3 
562 -STATIC VOLTAGE REGULATOR--EX2000R 
334 -PEECC MOTOR CONTROL CENTER (333) 
335 -BUS DUCT 
338 -CUSTOMER 480V SUPPLY 
339 -JB298 PEECC LEVEL 3 (333) 
348 -JB077A ACCESSORY BASE FP (119) 
363 -JB130 GAS FUEL MODULE (171) 
381 -JB021A TURBINE OFF BASE RACK LEVEL 4 
387 -JB020G TURBINE COMPARTMENT LOW LEVEL (250) 
390 -JB034 TURBINE ROOF LOW LEVEL (121) 
392 -JB004 ACCESSORY BASE LEVEL 4 (119) 
428 -JB090 COOLING WATER MODULE LEVEL 3 (161) 
438 -JB090A COOLING WATER MODULE LEVEL 4 (161) 
441 -JB131 GAS FUEL MODULE LEVEL 4 (171) 
447 -INLET HEATING CONTROL VALVE 
449 -JB078 TURB. AIR INLET FILTER COMPARTMENT (157) 
455 -JB297 AIR PROCESS SKID LEVEL 3 (172) 
456-JB010 WATER WASH SKID LEVEL 3 (252) 
514 -CUSTOMER SWITCHGEAR 
562 -STATIC VOLTAGE REGULATOR--EX2000R (333) 
563 -JB386 GAS SCRUBBER LEVEL 3 (158) 
581 -JB005N GEN. NEUTRAL ACCESSORIES COMPo LEVEL 3 (280) 
611 -INLET HEATING ISOLATION VALVE 
622 -FUEL GAS HEATER CONTROL PANEL 
GENERAL ELECTRIC COMPANY•~~=G=E==p=O=~=e=r=G__e_n_e_ra_t_io__n ________ ~
DRAWN 
DAVID H MATTICE 01-07-26 
SIZE 
~ 
CAGE CODE DWGNO 
377A4380 
ISSUED DOCUMENT SERVICES 01-07-26 SCALE NONEI I SHEET 4

+ (GR0730) 


.. 


l'g IREVC I + 
LOCATION DESCRIPTIONS (continued) 
742 -SITE LIGHTS 
751 -FLAME DETECTOR INTERFACE MODULE PRIMARY 
752 -FLAME DETECTOR INTERFACE MODULE SECONDARY 
753 -JB309 FUEL GAS HEATING SKID LEVEL 3 
901 -CUSTOMER GROUND GRID 
938 -CEMS SYSTEM 
939 -UNIT AREA OUTDOOR LIGHTING 
(Stamp comment
#41 dborgstadt
12/19/2010 12:56:24 PM
blank)
GENERAL ELECTRIC COMPANY•~~=G=E==p=O=~=e=r=G__e_n_e_ra_t_io__n ________ ~
DRAWN 
DAVID H MATTICE 01-07-26 
SIZE 
~ 
CAGE CODE DWGNO 
377A4380 
ISSUED DOCUMENT SERVICES 01-07-26 SCALE NONEI I SHEET 5

+ (GR0730) 


.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:56:21 PM
blank)
SOZEAIUWj,'7A4380 Ig I"EVc I + 
CUSTOMER SUPPLIED CABLES 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C001 101 136 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
19 COND 
C006 101 363 LEVEL(1) \ 18AWG 1 CABLE-18 TW INSTRUMENTATION 
36 COND SHLD PAIRS SIGNALS 
C009A 234 751 LEVEL(3S) \ 18AWG 1 CABLE-4 TW SHLD FLAME DETECTORS 28FD 
8COND PI\IRS (2WIRE) 
C009B 234 752 LEVEL(3S) \ 18AWG 1 CABLE-4 TW SHLD FLAME DETECTORS 28FD 
8COND PAIRS (2WIRE) 
C012 334 392 LEVEL(4) \ 4AWG 1 CABLE 125VDC SUPPLY 88QE-1 15 
3COND 
C013C 334 392 LEVEL(4) \ 10AWG 1 CABLE 3 PH SUPPLY 88TM-1 15 
3COND 
C014 101 363 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
37 COND 
con 101 135 LEVEL(1) \ 18AWG 1 CABLE-18 TW INSTRUMENTATION 
36 COND SHLD PAIRS SIGNALS RTDS 
C018 101 135 LEVEL(1S) \ 18AWG 1 CABLE-9 PAl R THERMOCOUPLES 
18 COND CHROM-ALUM TiC 
C022 227 363 LEVEL(2) \ 18AWG 1 CABLE-3 TW SHLD GAS DETECTORS 45HA-7 
9COND TRIADS 45HA-8 
C027 118 334 LEVEL(4) \ 2AWG 1 CABLE 3 PH. SUPPLY 88QA-1 15 
3COND 
C028 334 392 LEVEL(4) \ 8AWG 1 CABLE 3 PH. SUPPLY 88HQ-1 15 
3COND 
C037 101 115 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 15 
37 COND 
C038 101 234 LEVEL(1) \ 18AWG 1 CABLE-18 TW INSTRUMENTATION 
36 COND SHLD PAIRS SIGNALS 
C039 101 233 LEVEL(1S) \ 18AWG 1 CABLE-9 PAl R THERMOCOUPLES 
18 COND CHROM-ALUM TiC 
C041 101 233 LEVEL(1S) \ 18AWG 1 CABLE-9 PAl R THERMOCOUPLES 
18 COND CHROM-ALUM TiC 
C042 101 230 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
19 COND 
C049 102 146 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS GEN 15 
37 COND BREAKER 
C055A 334 381 LEVEL(4) \ 8AWG 1 CABLE 3 PH. SUPPLY 23HT-1 
3COND 
C055B 334 381 LEVEL(4) \ 8AWG 1 CABLE 3 PH. SUPPLY 23HT-2 
3COND 
C059 133 334 LEVEL(4) \ 10AWG 1 CABLE 3 PH. SUPPLY 23HG-1,-3,-5 
3COND 
C071 128 334 LEVEL(4) \ SIZED BY 3 PH. SUPPLY 88TK-1 
3COND CUSTOMER 
C072 129 334 LEVEL(4) \ SIZED BY 3 PH. SUPPLY 88TK-2 
3COND CUSTOMER 
C073 101 387 LEVEL(1S) \ 18AWG 1 CABLE-18 PR THERMOCOUPLES 15 
36 COND CHROM-ALUM TiC 
C074 101 387 LEVEL(1S) \ 18AWG 1 CABLE-18 PR THERMOCOUPLES 15 
36 COND CHROM-ALUM TiC 
C076 101 135 LEVEL(1) \ 18AWG 1 CABLE-9 TW SHLD INSTRUMENTATION 
18 COND PAIRS SIGNALS 
C077 146 334 LEVEL(4) \ 8AWG 1 CABLE 3 PH. SUPPLY 15 
3COND 
C080 146 335 LEVEL(3) \ 12AWG 1 CABLE 23BO 
3COND 
C083 102 146 LEVEL(3) \ 10AWG 1 CABLE VT SIGNALS 15 
12 COND 
C094B 135 562 LEVEL(1) \ 18AWG 1 CABLE-4 TW SHLD KA TO EXCITER 
8COND PAIRS 
C096 101 363 LEVEL(1) \ 18AWG 1 CABLE-18 TW INSTRUMENTATION 
36 COND SHLD PAIRS SIGNALS 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 6 + (GR0730) 

.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:56:18 PM
blank)
SOZEAIUWj,'7A4380 1"1' I"EVc I + 
CUSTOMER SUPPLIED CABLES (continued) 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C102 334 392 LEVEL(4) \ 8AWG 1 CABLE 3 PH. SUPPLY 23QT-1,-2 15 
3COND 
C117A 125 208 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD PROXIMITORS 
18 COND TRIADS 
C117B 126 208 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD PROXIMITORS 15 
18 COND TRIADS 
C117C 127 208 LEVEL(1) \ 18AWG 1 CABLE-3 TW SHLD PROXIMITORS 15 
9COND TRIADS 
C123 136 562 LEVEL(3) \ 10AWG 1 CABLE 64F EXCITER FIELD 15 
6COND 
C125 334 392 LEVEL(4) \ 10AWG 1 CABLE 3PH SUPPLY 23HA-3 & 15 
5COND 23HT-3 
C128 101 231 LEVEL(3) \ 12AWG 1 CABLE 26HT-1,-3 
6COND 
C135 284 348 LEVEL(2S) \ 18AWG 1 CABLE-9 TW SHLD FIRE DETECTORS CIRCUIT 
18 COND PAIRS (A) 
C136 284 348 LEVEL(2S) \ 18AWG 1 CABLE-9 TW SHLD FIRE DETECTORS CIRCUIT 
18 COND PAIRS (B) 
C145 208 325 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD PROXIMITORS 15 
18 COND TRIADS 
C148 146 562 LEVEL(3) \ 10AWG 1 CABLE CONTROL CURRENT 15 
4COND TRANSFORMERS 
C149 334 441 LEVEL(4) \ 8AWG 1 CABLE 1 PH. SUPPLY 23VS-1 
3COND 
C161 115 339 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATERS, AC 15 
12 COND LIGHTS 
C171 227 234 LEVEL(2) \ 18AWG 1 CABLE-3 TW SHLD GAS DETECTORS 45HT-1 
9COND TRIADS 45HT-2 
C172 114 201 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD RTDS 88CR-1 
18 COND TRIADS 
C182 101 231 LEVEL(3) \ 12AWG 1 CABLE 20TW DEVICES 
12 COND 
C190 128 339 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATER 23TK-1 
2COND 
C191 101 128 LEVEL(3) \ 12AWG 1 CABLE 63TK-1 
3COND 
C192 129 339 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATER 23TK-2 
2COND 
C193 101 129 LEVEL(3) \ 12AWG 1 CABLE 63TK-2 
3COND 
C199 122 334 LEVEL(4) \ 8AWG 1 CABLE 3 PH. SUPPLY 88BT-1 
3COND 
C199A 122 339 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATER 23BT-1 
2COND 
C200 101 233 LEVEL(1S) \ 18AWG 1 CABLE-18 PR THERMOCOUPLES 
36 COND CHROM-ALUM TiC 
C201 101 390 LEVEL(1) \ 18AWG 1 CABLE-4 TW SHLD 96CD-1A 96CD-1B 96CD-1C 
8COND PAIRS 
C216 339 363 LEVEL(3) \ 12AWG 1 CABLE AC LIGHTS 
3COND 
C217 339 363 LEVEL(3) \ 10AWG 1 CABLE DC STANDBY LIGHTING 
2COND 
C219 136 339 LEVEL(3) \ 12AWG 1 CABLE LIGHTS --RECEPTACLES 
12 COND 
C235A 102 146 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 15 
12 COND 21-23,60-62 
C235B 102 146 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 15 
12 COND 27-29, 48-50 
C235C 108 146 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 
12 COND 24-26 
C236A 102 581 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 15 
12 COND 1-6,NGR 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 7 + (GR0730) 

.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:56:13 PM
blank)
SOZEAIUWj,'7A4380 I'il' I"EVc I + 
CUSTOMER SUPPLIED CABLES (continued) 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C236B 102 581 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 15 
12 COND 7-9 
C236C 102 146 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 15 
12 COND 30-32 
C237 146 334 LEVEL(4) \ 6AWG SINGLE 125VDC BREAKER CLOSE 15 
2COND CONDUCTORS CIRCUIT 
C249 339 581 LEVEL(3) \ 10AWG 1 CABLE 23HG-20 15 
3COND 
C251 334 392 LEVEL(4) \ 6AWG 1 CABLE 3 PH. SUPPLY 23HA-1 
3COND 23HA-2 
C256 101 230 LEVEL(3) \ 10AWG 1 CABLE 120VAC SUPPLY -
3COND IGNITION TRANSFORMERS 
C257 101 231 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
12 COND 
C270 115 339 LEVEL(3) \ 12AWG 1 CABLE LIGHTS, 26QL-1 15 
12 COND 
C285 101 363 LEVEL(1S) \ 18AWG 1 CABLE-3 PAl R THERMOCOUPLES FTG-1A,BCOND 
CHROM-ALUM TIC 1 B,-2A -2B 
C401 183 254 LEVEL(4) \ SIZED BY 480V TO CUSTOMER UNIT 11 
3COND CUSTOMER #1 
C402 334 939 LEVEL(4) \ SIZED BY 480V UNIT LIGHTING 
3COND CUSTOMER 
C403 334 742 LEVEL(4) \ SIZED BY 480V SITE LIGHTING 
3COND CUSTOMER 
C404 334 938 LEVEL(4) \ SIZED BY 480V CEM LOADS 
3COND CUSTOMER 
C406 182 334 LEVEL(4) \ SIZED BY 480V ALTERNATIVE POWER 13 
3COND CUSTOMER TO STEPUP TRANS. 
COOLING 
C407 182 334 LEVEL(4) \ SIZED BY 480V NORMAL POWER TO 12 
3COND CUSTOMER STEPUP TRANS. COOLING 
C408 001 334 LEVEL(4) \ SIZED BY 480V W ELDI NG OUTLETS 
3COND CUSTOMER 
C409A 182 334 LEVEL(3) \ 10AWG 1 CABLE 125VDC TO LOAD BREAK 12 
2COND CKT SWITCHER 
C409B 182 334 LEVEL(3) \ 10AWG 1 CABLE 125VDC TO TRANSFORMER 13 
2COND ANNUNCIATOR 
C410A 254 334 LEVEL(3) \ 10AWG 1 CABLE 125VDC H2235 RELAY RACK 12 
2COND IN ROCS TRAILER 
REGULAR 
C410B 254 334 LEVEL(3) \ 10AWG 1 CABLE 125VDC H2235 RELAY RACK 13 
2COND IN ROCS TRAILER BACKUP 
C411 183 622 LEVEL(4) \ SIZED BY 480V SUPPLY TO GAS 
3COND CUSTOMER HEATER CONTROL PANEL 
C413 622 753 LEVEL(1) \ 18AWG 1 CABLE-3 PAl R THERMOCOUPLES 
6COND CHROM-ALUM TIC 
C414 622 753 LEVEL(3) \ 12AWG 1 CABLE GAS FUEL HEATER 
3COND EMERGENCY STOP 
C414A 101 622 LEVEL(3) \ 12AWG 1 CABLE FUEL GAS HEATER 
7COND CONTROLLS 
C415 183 338 LEVEL(4) \ SIZED BY CUTOMER 480V SUPPLY TO AUX 
3COND TRANS 
C417A 102 102 LEVEL(3) \ 10AWG 1 CABLE crs 7-9 & 30-31 SIGNALS 11 
12 COND GCP UNIT #2 TO GCP UNIT 
111 
C418A 102 102 LEVEL(3) \ 10AWG 1 CABLE crs 27-29. 48-50 SIGNALS 
12 COND GCP UNIT #2 TO GCP UNIT 
#1 
C420A 102 254 LEVEL(3) \ 10AWG 1 CABLE CUSTOMER CTS 39-41 TO 13 
4COND 87T 
C420B 102 254 LEVEL(3) \ 10AWG 1 CABLE CUSTOMER CTS 42-44 TO 12 
4COND 87U 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 8 + (GR0730) 

.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:56:10 PM
blank)
SOZEAIUWj,'7A4380 1'1l' I"EVc I + 
CUSTOMER SUPPLIED CABLES (continued) 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C421 108 108 LEVEL(3) \ 12AWG 1 CABLE EVEN UNIT TO 000 UINT 
12 COND CONTACTS 
C421A 108 108 LEVEL(3) \ 12AWG 1 CABLE ODD UNIT TO EVEN UINT 
12 COND CONTACTS 
C421B 108 108 LEVEL(3) \ 12AWG 1 CABLE EVEN UNIT TO ODD UINT 
12 COND CONTI\CTS 
C421C 108 108 LEVEL(3) \ 12AWG 1 CABLE ODD UNIT TO EVEN UINT 
12 COND CONTACTS 
C422 108 108 LEVEL(3) \ 12AWG 1 CABLE ODD UNIT TO EVEN UNIT 
6COND CONTACTS 
C422A 108 108 LEVEL(3) \ 12AWG 1 CABLE EVEN UNIT TO 000 UNIT 
6COND CONTACTS 
C426 108 254 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD 96GR-1, 96AW-1, 96GG-2, 
12 COND PAIRS 96GV-1 
C426A 108 254 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 96GG'2 
3COND TRIAD 
C428 101 146 LEVEL(3) \ 12AWG 1 CABLE 52G FAN ALARMS 
BCOND 
C473 101 387 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 39V-3A 15 
2COND PAIR 
C474 101 387 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 39V-3B 15 
2COND PAIR 
C480 334 514 LEVEL(3) \ 12AWG 1 CABLE 120VAC FOR CUSTOMER 
3COND AUX POWER SUBSTATION 
COMPARTMENT 
C481 334 514 LEVEL(3) \ 10AWG 1 CABLE 125VDC FOR CUSTOMER 
2COND AUX POWER SUBSTATION 
C512 101 449 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
7COND 
C513A 101 157 LEVEL(1S) \ 18AWG 1 CABLE-1 CHROMAT-
ID-1 THERMOCOUPLE 
2COND ALUM TIC PAIR 
C513B 101 157 LEVEL(1S) \ 18AWG 1 CABLE-1 CHROMAT-
ID-2 THERMOCOUPLE 
2COND ALUM TIC PAIR 
C513C 101 157 LEVEL(1S) \ 18AWG 1 CABLE-1 CHROMAT-
ID-3 THERMOCOUPLE 
2COND ALUM TIC PAIR 
C515 339 449 LEVEL(3) \ 6AWG 1 CABLE 120./240VAC SUPPLY 
3COND 
C516A 101 447 LEVEL(3) \ 12AWG 1 CABLE 20TH-1 
2COND 
C516E 101 611 LEVEL(3) \ 12AWG 1 CABLE 33TH-3 
2COND 
C517A 101 447 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 96TH-1 
2COND PAIR 
C517B 101 447 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 65EP-3 
2COND PAIR 
C517D 101 447 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 96BH-1 
2COND PAIR 
C517E 101 447 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 96BH-2 
2COND PAIR 
C531 101 428 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
6COND 
C532 339 428 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
12 COND 
C533 334 438 LEVEL(4) \ SIZED BY 3 PH. SUPPLY 8BFC-1 
3COND CUSTOMER 
C534 334 43B LEVEL(4) \ SIZED BY 3 PH. SUPPLY BBFC-2 
3COND CUSTOMER 
C535 334 43B LEVEL(4) \ SIZED BY 3 PH. SUPPLY BBFC-3 
3COND CUSTOMER 
C537 334 43B LEVEL(4) \ SIZED BY 3 PH. SUPPLY BBWC-1 
3COND CUSTOMER 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 9 + (GR0730) 

.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:56:06 PM
blank)
SOZEAIUWj,'7A4380 110 I"EVc I + 
CUSTOMER SUPPLIED CABLES (continued) 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C538 334 438 LEVEL(4) \ SIZED BY 3 PH. SUPPLY 88WC-2 
3COND CUSTOMER 
C544 339 428 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATERS 
12 COND 
C549 102 254 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD METERING 
18 COND TRIADS 
C549A 108 254 LEVEL(1) \ 18AWG 1 CABLE-6 TW SHLD METERING 
18 COND TRIADS 
C550A 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL CONTROL 
19 COND SIGNALS OUT 
C550B 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL CONTROL 
19 COND SIGNALS OUT 
C550C 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL CONTROL 
19 COND SIGNALS OUT 
C550D 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL CONTROL 
19 COND SIGNALS OUT 
C551A 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL CONTROL 
12 COND SIGNALS IN 
C551B 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL CONTROL 
12 COND SIGNALS IN 
C551C 101 254 LEVEL(3) \ 12AWG 1 CABLE DIGITAL OUTPUTS TO 
12 COND CUSTOMER ALARM PANEL 
C553A 101 254 LEVEL(1) \ 18AWG 1 CABLE-9 TW SHLD ANALOGS IN/OUT 
18 COND PAIRS 
C553B 101 254 LEVEL(1) \ 18AWG 1 CABLE-9 TW SHLD ANALOGS IN/OUT 
18 COND PAIRS 
C554 101 254 LEVEL(3) \ 12AWG 1 CABLE REMOTE EMERGENCY TRIP 
4COND R5E 
C575 149 201 LEVEL(5) \ SIZED BY 3 PH. SUPPLY 88CR-1 
3COND CUSTOMER 
C583 183 334 LEVEL(4) \ 2 PER PH. 3PH. 800 AMP SUPPLY 
6COND FEEDER MCC1-AC 
C584 183 334 LEVEL(4) \ 2 PER PH. 3PH. 800 AMP SUPPLY 
6COND FEEDER MCC2-AC 
C590 101 201 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
6COND 
C591 108 183 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 
2COND 51TN-2 
C593 108 183 LEVEL(3) \ 10AWG 1 CABLE CURRENT TRANSFORMERS 
4COND 50/51AT-2 
C596 201 334 LEVEL(3) \ 10AWG 1 CABLE 125VDC CONTROL POWER 
2COND 
C598 201 329 LEVEL(5) \ SIZED BY MEDIUM VOLTAGE SUPPLY 
3COND CUSTOMER 
C607 101 225 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 96TD-1 
2COND PAIR 
C607A 225 339 LEVEL(3) \ 12AWG 1 CABLE 120VAC SUPPLY 96TD-1 
3COND 
C610A 102 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86G 1 CONTACTS TO 
12 COND CUSTOMER 
C610B 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86G2 CONTACTS TO 
12 COND CUSTOMER 
C610C 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86RE CONTACTS TO 
12 COND CUSTOMER 
C610D 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86AT CONTACTS TO 
12 COND CUSTOMER 
C610E 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86BF CONTACTS TO 
12 COND CUSTOMER 
C610F 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86G-1 CONTACTS TO 
12 COND CUSTOMER 
C610FA 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86G-2 CONTACTS TO 
12 COND CUSTOMER 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 10 + (GR0730) 

.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:56:03 PM
blank)
SOZEAIUWj,'7A4380 111 I"EVc I + 
CUSTOMER SUPPLIED CABLES (continued) 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C610FB 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86BF CONTACTS TO 
12 COND CUSTOMER 
C610FC 108 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86RE CONTACTS TO 
12 COND CUSTOMER 
C610H 102 254 LEVEL(3) \ 12AWG 1 CABLE 86T1 CONTACTS TO 
12 COND CUSTOMER 
C610HA 102 254 LEVEL(3) \ 12AWG 1 CABLE AUX 86T-1 CONTACTS TO 
12 COND CUSTOMER 
C610J 108 254 LEVEL(3) \ 12AWG 1 CABLE 86AT CONTACTS TO 
12 COND CUSTOMER 
C610V 102 254 LEVEL(3) \ 12AWG 1 CABLE CUSTOMER INTERLOCKS 
12 COND 
C610W 108 254 LEVEL(3) \ 12AWG 1 CABLE CUSTOMER INTERLOCKS 
12 COND 
C611 102 254 LEVEL(3) \ 12AWG 1 CABLE CUSTOMER TRIPS AND 
12 COND PERMISSIVES 
C611A 102 254 LEVEL(3) \ 12AWG 1 CABLE CUSTOM ER TRI PS 
6COND 
C615D 101 156 LEVEL(1) \ 18AWG 1 CABLE-1 TW SHLD 96FM-1A 
2COND PAIR 
C667-1 101 456 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS UNIT #1 11 
12 COND 
C667-2 101 456 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS UNIT #1 
12 COND 
C667-3 101 456 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS UNIT #1 
12 COND 
C667-4 101 456 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS UNIT #1 
12 COND 
C669 183 252 LEVEL(4) \ SIZED BY 3 PH. 480V SUPPLY WATER 11 
3COND CUSTOMER WASH SKID 
C671 101 176 LEVEL(3) \ 12AWG 1 CABLE 63QV-1 
3COND 
C672 176 334 LEVEL(4) \ SIZED BY 3 PH. SUPPLY 88QV-1 
3COND CUSTOMER 
C672A 176 339 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATER 23QV-2 
2COND 
C67S 101 257 LEVEL(1) \ 18AWG 1 CABLE-9 TW SHLD 5 TWO WIRE TRANSDUCER 
18 COND PAIRS PACKAGE 
C725 339 455 LEVEL(3) \ 12AWG 1 CABLE CONTROL POWER SUPPLY 
3COND 
C727 101 455 LEVEL(3) \ 12AWG 1 CABLE 63AD-4 
6COND 
C743 102 201 LEVEL(3) \ 10AWG 1 CABLE 59CM RELAY 
2COND 
C745A 146 329 LEVEL(5) \ SIZED BY 13.8KV TO TRANSFORMER 
3COND CUSTOMER PRIMARY 
C745B 183 329 LEVEL(5) \ SIZED BY 13.8KV TO TRANSFORMER 
3COND CUSTOMER PRIMARY 
C776 136 151 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
5COND 
C777 136 151 LEVEL(3) \ 12AWG 1 CABLE 120VAC SUPPLY 34GF-1 
2COND 
C809 334 441 LEVEL(4) \ 10AWG 1 CABLE 3 PH. SUPPLY 88VL-2 
3COND 
C809A 339 441 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATER 23VL-2 
2COND 
C817 334 441 LEVEL(4) \ 10AWG 1 CABLE 3 PH. SUPPLY 88VL-1 
3COND 
C817A 339 441 LEVEL(3) \ 10AWG 1 CABLE MOTOR HEATER 23VL-1 
2COND 
C819 101 563 LEVEL(3) \ 12AWG 1 CABLE 71 GS-1 ,-2A,-2B,-2C 
19 COND 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 11 + (GR0730) 

(Stamp comment
#41 dborgstadt
12/19/2010 12:55:59 PM
blank)
SOZEAIUWj,'7A4380 112 I"EVc I + 
CUSTOMER SUPPLIED CABLES (continued) 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
C849 201 339 LEVEL(3) \ 10AWG 1 CABLE 23LC HEATER 
3COND 
C870 101 284 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
12 COND 
C871 284 339 LEVEL(3) \ 12AWG 1 CABLE 120VAC SUPPLY 
3COND 
C872 284 339 LEVEL(3) \ 12AWG 1 CABLE CONTROL SIGNALS 
12 COND 
C874 284 339 LEVEL(4) \ 10AWG 1 CABLE 3 PH SUPPLY 88RC-1 
3COND 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 12 
.. ~ 

+ (GR0730) 


.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:54 PM
blank)
SOZEAIUWj,'7A4380 113 I"EVc I + 
CUSTOMER SUPPLIED GROUND CABLES 
cable to from level I diameter I gauge makeup purpose special 
number #cond bend rad notes 
CG 1 D07 254 901 LEVEL(4) \ 1/0 AVVG BARE CONDUCTOR GROUND GRID CABLE 
1 COND 
CG 1 D08 333 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG1D31 230 901 LEVEL(4) \ 1/0 AWG BARE CONDUCTOR GROUND GRID CABLE 
1 COND 
CG1D32 231 901 LEVEL(4) \ 1/0 AWG BARE CONDUCTOR GROUND GRID CABLE 
1 COND 
CG1D33 233 901 LEVEL(4) \ 1/0 AWG BARE CONDUCTOR GROUND GRID CABLE 
1 COND 
CG 1 034 234 901 LEVEL(4) \ 1/0 AWG BARE CONDUCTOR GROUND GRID CABLE 
1 COND 
CG1D38 381 901 LEVEL(4) \ 1/0 AWG BARE CONDUCTOR GROUND GRID CABLE 
1 COND 
CG1051 280 901 LEVEL(4) \ 4/0 AVVG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG1D59 335 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG9D2 157 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG9D6 182 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG9D7 146 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG910 161 901 LEVEL(4) \ 4/0 AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG914 121 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG915 119 901 LEVEL(4) \ 4/0 AVVG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG920 134 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG926 171 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG927 176 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG928 252 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 11 
2COND CONDUCTORS 
CG929 172 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG931 183 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG933 201 901 LEVEL(4) \ 4/0 AVVG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG954 158 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG964 128 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG965 129 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
CG983 283 901 LEVEL(4) \ 4/0AWG BARE GROUND GRID CABLE 
2COND CONDUCTORS 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI I SHEETDOCUMENT SERVICES 01-07-26 13 + (GR0730) 

SOZEAIUWj,'7A4380 114 I"EVc I 

+ 

001 WELDING RECEPTACLE ONE 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:50 PM
blank)
cable to I lev I #cnd I Qauae 

C408 334 PEECC MOTOR CONTROL CENTER I 4 I 3 I 

.. ~ 

SIZE 

CAGE CODE 

DWGNO

GENERAL ELECTRIC COMPANY

•GE Power Generation 

377A4380

A

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SCALE 

I SHEET

DOCUMENT SERVICES 01-07-26 

NONEI 14 

+ (GR0730) 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:47 PM
blank)
101 TURBINE CONTROL PANEL 

cable 
G001 
G006 
C014 
C017 
C018 
G037 
C038 
C039 
C041 
C04L 
C073 
C074 
C076 
CO"5 
I to 
136 JB005B GENERA~ OR lEVEL 
363 JB130 GAS FUEL 
363 JB130 GAS FUEL MODULE 
135 JB005A GENERA~ OR' LOW LEVEl 
135 JB005A LOW LEVEL 
15 JB002 A JRY BASE _EVEl3 
234 JB020B ~NEOFF BASE RACK OW _EVEL 
233 JB020A ~NEOFF BASE RACK OW _EVEL 
I 233 JB020A TURBINE OFF BASE RACK LOW LEVEL 
L3U Je018A UKelNe ~eA~e KACK leVel 
38, JB020G TURBINE :N1 "W LEVEl 
38, JB020G TURBINE "W LEVEl 
135 JB005A GENERA ~ LOW LEVEl 
353 Je' 3U e;A~ rUel MUUUle 
LEVEl 3 
LEVEl 3 
lev #cnd 
3 19 
1 36 
3 37 
1 36 
1S 18 
3 37 
1 36 
IS 18 
1S 18 
'" IS 36 
IS 36 
1 18 
1 35 
aauae 
12AWG 
18AWG 
12AWG 
18AWG 
18AWG 
12AWG 
18AWG 
18AWG 
18AWG 
lLAwe; 
18AWG 
18AWG 
18AWC 
WAwe; 
C20 390 JB034 JRBINE ROOF 'JW LEVEl 1 8 18 AWG 
C256 230 JB019A URBINE OFF BASE RACK LEVEl 3 3 3 'AWG 
~,-------H2~':3+--,lJT5'fB,(O*,19B'r-'iU~RBe;;IIIN~EO*,FF",'B",A,T':SE-"",RA"'C:"---KL="-"EV -==-'EI"----3___________1--ii3~-'.z;2'---t~'~2,-'iii'iAW",CGHI C285 353 Je' 3U e;A~ rUel MUUUle 1~ W AWe; 
:4 I 622 (C OL PANEL 
13( 
161 
146 ~AI I 
:AI 
:A 1 
I EA I 'AlV 
I ".A I ISC IN V, IE 
I ,A'I VAL 
VEl 
lENT 
I ,A' I IAl 
~~~~~~~'~~~'~A' ,VAL 
7E I I V IE 
H JLE LEVEL 3 
OA 
OB 
OG ,VI 
C550D 254 JST~DEVI 3 19 12 AWG 
g~~~~ ~~:~~l~DEVIC §tt~ ~ 1~ ~~~~~ 
C551C 1254 CUSTOMER DEVI 3 12 12 AWG 
G553A 254 DE' 1 18 18 AWG 
C553B 254 US1i5MEROEVIC ~LS 1 18 18AWG 
C554 254 US1 i5MER =LS 3 4 12 AWG 
C590 1201 LIMIT AMP ~--------------------------4-3~-~6~,~,;2~AW~CG~ 
C501 LLO KelAIIVe HUMIUII Y 1 L W AWe; 
C615D 156 FUEL GAS FWW DEVICES 1 2 18 AWG 
~667-1 1456 JB010 WATER WASH SKID LEVEL 3 3 12 12 AWG 
~~C~66;;7~~-+~4t,5~6~~010 WATERWASH~~'O~L~E,/E~L3~-------------~3~-~'21_-'~2,A~WC~
[;66/_ 14bb JB01U WA I eK WA~H SKlu leVel 3 3 lL lL Awe; 
,R WASH lEVEL 3 WI 
BII 
"W _EVEL 
I .'N( I I 
;AS 3 
I PA ~E 
,AI 
,AWC 
SIZE 

CAGE CODE 

DWGNO

• GENERAL ELECTRIC COMPANY 
~~=G=E==p=o=~=e=r=G--e-n-e-ra-t-io--n--------~~ 

377A4380 

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SHEET 

DOCUMENT SERVICES 01-07-26 

15 

(GR0730) 


+ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:43 PM
blank)
102 GENERATOR CONTROL PANEL 

SOZEAIUWj,'7A4380 116 I"EVc I 

cable 
C049 
C083 
C235A 
C235B 
C236A 
C236B 
C236C 
C417A 
C418A 
C420A 
C420B 
C549 
C610A 
C610H 
C610HA 
C610V 
C611 
C611A 
C743 
to 
146 METALCLAD SWITCHGEAR 
146 METALCLAD SWITCHGEAR 
146 METALCLAD SWITCHGEAR 
146 METALCLAD SWITCHGEAR 
581 JB005N GEN. NEUTRAL ACCESSORIES COMP. LEVEL 3 
581 JB005N GEN. NEUTRAL ACCESSORIES COMP. LEVEL 3 
146 METALCLAD SWITCHGEAR 
102 GENERATOR CONTROL PANEL 
102 GENERATOR CONTROL PANEL 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
201 LIMIT AMP 
lev 
3 
3 
3 
3 
3 
3 
3 
3 
3 
3 
3 
1 
3 
3 
3 
3 
3 
3 
3 
#cnd 
37 
12 
12 
12 
12 
12 
12 
12 
12 
4 
4 
18 
12 
12 
12 
12 
12 
6 
2 
Qauae 
12AWG 
10AWG 
10AWG 
10AWG 
10AWG 
10AWG 
10AWG 
10AWG 
10AWG 
10AWG 
10AWG 
18AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
10AWG 

108 AUXILIARY RELAY PANEL 

.. ~ 

cable 
C235C 
C421 
C421A 
C421B 
C421C 
C422 
C422A 
C426 
C426A 
C549A 
C591 
C593 
C610B 
C610C 
C610D 
C610E 
C610F 
C610FA 
C610FB 
C610FC 
C610J 
C610W 
to 
146 METALCLAD SWITCHGEAR 
108 AUXILIARY RELAY PANEL 
108 AUXILIARY RELAY PANEL 
108 AUXILIARY RELAY PANEL 
108 AUXILIARY RELAY PANEL 
108 AUXILIARY RELAY PANEL 
108 AUXILIARY RELAY PANEL 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
183 AUXILIARY POWER TRANSFORMER 
183 AUXILIARY POWER TRANSFORMER 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES--PANELS 
254 CUSTOMER DEVICES PANELS 
lev 
3 
3 
3 
3 
3 
3 
3 
1 
1 
1 
3 
3 
3 
3 
3 
3 
3 
3 
3 
3 
3 
3 
#cnd 
12 
12 
12 
12 
12 
6 
6 
12 
3 
18 
2 
4 
12 
12 
12 
12 
12 
12 
12 
12 
12 
12 
gauge 
10AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
18AWG 
18AWG 
18AWG 
10AWG 
10AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 
12AWG 

114 JB001 ACCESSORY BASE LOW LEVEL 

cable to I lev I #cnd I !lau!le I 

C172 201 LIMIT AMP I 1 I 18 I 18AWG I 

SIZE 

CAGE CODE 

DWGNO

GENERAL ELECTRIC COMPANY

•GE Power Generation 

377A4380

A

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SHEET

SCALE 

DOCUMENT SERVICES 01-07-26 

16

NONEI 

+ (GR0730) 


.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:40 PM
blank)
SOZEAIUWj,'7A4380 11'7 I"EVc I + 
115 JB002 ACCESSORY BASE LEVEL 3 
cable I to lev #cnd aauae 
C037 URBINE CONTROL PANEL 37 12AWG 
C161 339 JB298 PEECC LEVEl 3 3 12 'AWG 
C270 339 JB298 PEECC LEVEl 3 3 2 12AWG 
118 ACCESSORY BASE MOTORS 
cable to I lev I #cnd I gauge I 
C027 334 PEECC MOTOR CONTROL CENTER I 4 I 3 I 2AWG I 
119 ACCESSORY BASE 
cable to I lev I #cnd I QauQe I 
CG915 901 CUSTOMER GROUND GRID I 4 I 2 I 4/0 AWG I 
121 TURBINE BASE 
cable to I lev I #cnd I gauge I 
CG914 901 CUSTOMER GROUND GRID I 4 I 2 I 4/0 AWG I 
122 TURBINE ROOF MOUNTED DEVICES 
cable to I lev I #cnd I QauQe I 
C199 334 PEECC MOTOR CONTROL CENTER I 4 I 3 I 8AWG I 
C199A 339 JB298 PEECC LEVEL 3 I 3 I 2 I 10AWG I 
125 JB055 TURBINE BASE LOW LEVEL 
cable to I lev I #cnd I Qauae I 
C117A 208 VIBRATION MONITOR PANEL I 1 I 18 I 18AWG I 
126 JB056 TURBINE BASE LOW LEVEL 
I cable Ito I lev I #cnd I gauge I 
C117B 208 VIBRATION MONITOR PANEL I 1 I 18 I 18AWG I 
127 JB085 LOAD GEAR COMPARTMENT LOW LEVEL 
cable to I lev I #cnd I aauae I 
C117C 208 VIBRATION MONITOR PANEL I 1 I 9 I 18AWG I 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 17 + (GR0730) 

(Stamp comment
#41 dborgstadt
12/19/2010 12:55:37 PM
blank)
SOZEAIUWj,'7A4380 118 IREvc I + 
128 EXHAUST FRAME BLOWER 88TK-1 
cable to lev #cnd Qauae 
CO?1 334 PEECC MOTOR CONTROL CENTER 4 3 
C190 339 JB298 PEECC LEVEL 3 3 2 10AWG 
C191 101 TURBINE CONTROL PANEL 3 3 12AWG 
CG964 901 CUSTOMER GROUND GRID 4 2 4/0 AWG 
129 EXHAUST FRAME BLOWER 88TK-2 
cable I to lev #cnd QauQe 
C072 334 PEEC OL 4 3 
C192 339 JB298 PEECC LEVEl 3 3 2 'AWG 
C193 URBINE :ONTROL PANEL 3 3 12AWG 
,G965 190 US10MER lGRIC 4 2 4/0 AWG 
133 JB005C GENERATOR COMPARTMENT LEVEL 4 
cable to I lev I #cnd I gauge I 
C059 334 PEECC MOTOR CONTROL CENTER I 4 I 3 I 10AWG I 
134 GENERATOR COMPARTMENT 
cable to I lev I #cnd I gauge I 
CG920 901 CUSTOMER GROUND GRID I 4 I 2 I 4/0 AWG I 
135 JB005A GENERATOR COMPARTMENT LOW LEVEL 
136 JB005B GENERATOR COMPARTMENT LEVEL 3 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI 
SHEET 
DOCUMENT SERVICES 01-07-26 18 + (GR0730) 
.. ~ 

cable to lev #cnd gauge 
C01? 101 TURBINE CONTROL PANEL 1 36 18AWG 
C018 
CO?6 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
15 
1 
18 
18 
18AWG 
18AWG 
C094B 562 STATIC VOLTAGE REGULATOR--EX2000R 1 8 18AWG 

cable 
C001 
C123 
C219 
C776 
C?77 
to 
101 TURBINE CONTROL PANEL 
562 STATIC VOLTAGE REGULATOR--EX2000R 
339 JB298 PEECC LEVEL 3 
151 JB215 GENERATOR FILTER SEQUENCER 
151 JB215 GENERATOR FILTER SEQUENCER 
lev 
3 
3 
3 
3 
3 
#cnd 
19 
6 
12 
5 
2 
gauge 
12AWG 
10AWG 
12AWG 
12AWG 
12AWG 


.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:33 PM
blank)
SOZEAIUWj,'7A4380 119 IREvc I + 
146 METALCLAD SWITCHGEAR 
cable to lev #cnd Qauae 
C049 102 GENERATOR CONTROL PANEL 3 37 12AWG 
C077 334 PEECC MOTOR CONTROL CENTER 4 3 SAWG 
COSO 335 BUS DUCT 3 3 12AWG 
COS3 102 GENERATOR CONTROL PANEL 3 12 10AWG 
C14S 562 STATIC VOLTAGE REGULATOR--EX2000R 3 4 10AWG 
C235A 102 GENERATOR CONTROL PANEL 3 12 10AWG 
C235B 102 GENERATOR CONTROL PANEL 3 12 10AWG 
C235C 108 AUXILIARY RELAY PANEL 3 12 10AWG 
C236C 102 GENERATOR CONTROL PANEL 3 12 10AWG 
C237 334 PEECC MOTOR CONTROL CENTER 4 2 6AWG 
C428 101 TURBINE CONTROL PANEL 3 6 12 AWG 
C745A 329 CRANKING MOTOR TRANSFORMER 5 3 
CG907 901 CUSTOMER GROUND GRID 4 2 4/0 AWG 
149 CRANKING MOTOR 
cable to I lev I #cnd I QauQe I 
C575 201 LIMIT AMP I 5 I 3 I I 
151 JB2t5 GENERATOR FILTER SEQUENCER 
cable I to 
~ ~ 
I lev I #cnd I ~ C777 136 ~OO5B GENERA-8R LEVEL 3 I 3 I 2 I 
156 FUEL GAS FLOW DEVICES 
I cable Ito I lev I #cnd I gauge I 
C615D 101 TURBINE CONTROL PANEL I 1 I 2 I 1SAWG I 
157 TURBINE AIR INLET FILTER COMPARTMENT 
cable to lev #cnd gauge 
C513A 101 TURBINE CONTROL PANEL 1S 2 1SAWG 
C513B 101 TURBINE CONTROL PANEL 18 2 18AWG 
C513C 101 TURBINE CONTROL PANEL 1S 2 1SAWG 
CG902 901 CUSTOMER GROUND GRID 4 2 4/0 AWG 
158 GAS SCRUBBER 
cable to I lev I #cnd I Qauae I 
CG954 901 CUSTOMER GROUND GRID I 4 I 2 I 4/0 AWG I 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI 
SHEET 
DOCUMENT SERVICES 01-07-26 19 + (GR0730) 

.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:29 PM
blank)
SOZEAIUWj,'7A4380 I~o REVC I + 
161 COOLING WATER MODULE #1 
cable I to I lev I #cnd I aauae I 
eG910 90 CUS10MER lGR'C I 4 I 2 I 4/0 AWG I 
171 GAS FUEL (VALVE) MODULE 
~ I to I lev I #cnd I aauae I 
190 US10MER lGRIC I 4 I 2 I 4/0 AWG I 
172 AIR PROCESS SKID 
I cable Ito I lev I #cnd I gauge I 
CG929 901 CUSTOMER GROUND GRID I 4 I 2 I 4/0 AWG I 
176 LUBE OIL DEMISTER (TURBINE) 
cable to lev #cnd gauge 
C671 101 TURBINE CONTROL PANEL 3 3 12AWG 
C672 334 PEECC MOTOR CONTROL CENTER 4 3 
C672A 339 JB298 PEECC LEVEL 3 3 2 10AWG 
CG927 901 CUSTOMER GROUND GRID 4 2 4/0 AWG 
182 MAIN TRANSFORMER (STEP UP) 
~ I to lev #cnd aauae 
JJ4 ~ccCl OL 4 
A07 EC :c _CENTER 
409A EC 'AWG 
~ EC fill 11'AWG 
183 AUXILIARY POWER TRANSFORMER 
cable I to lev #cnd aauae 
C401 Lb4 C;U:;, OM cK 4 
GA! ROL PANEl 
OMI 'PI 
~ JL~ 
~NEL 'AWG 
PANEL 'AWG 
H~ 90 j:;, OMcH ~ 4/0 AWG 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 20 + (GR0730) 

SOZEAIUWj,'7A4380 

~1 I"EVc I 

+ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:15 PM
blank)
201 LIMIT AMP 

cable to lev #cnd Qauae 
C172 114 JB001 ACCESSORY BASE LOW LEVEL 1 18 18AWG 
C575 149 CRANKING MOTOR 5 3 
C590 101 TURBINE CONTROL PANEL 3 6 12AWG 
C596 334 PEECC MOTOR CONTROL CENTER 3 2 10AWG 
C598 329 CRANKING MOTOR TRANSFORMER 5 3 
C743 102 GENERI\TOR CONTROL PI\NEL 3 2 10l\WG 
C849 339 JB298 PEECC LEVEL 3 3 3 10AWG 
CG933 901 CUSTOMER GROUND GRID 4 2 4/0 AWG 

208 VIBRATION MONITOR PANEL 

I 
~ O~ 
:c 
1E 
~MI JT 
CJW LEVEL 
CJW LEVEL 
#c ,d 
W 

225 RELATIVE HUMIDITY SENSOR 

cable to lev #cnd gauge 
CS07 101 TURBINE CONTROL PANEL 1 2 18 AWG 
C607A 339 JB298 PEECC LEVEL 3 3 3 12AWG 

227 HAZARDOUS GAS MONITOR 

cable to I lev I #cnd I QauQe I 

C022 363 JB130 GAS FUEL MODULE I 2 I 9 I 18AWG I 

.. 
.. 
C171 234 JB020B TURBINE OFF BASE RACK LOW LEVEL I 2 I 9 I 18AWG I 

~ 

230 JBOt9A TURBINE OFF BASE RACK LEVEL 3 

cable to lev #cnd Qauae 
C042 101 TURBINE CONTROL PANEL 3 19 12AWG 
C256 101 TURBINE CONTROL PANEL 3 3 10AWG 
CG1031 901 CUSTOMER GROUND GRID 4 1 1/0AWG 

231 JBOt9B TURBINE OFF BASE RACK LEVEL 3 

gauge

cable 

to 

lev #cnd 

C128 101 TURBINE CONTROL PANEL 

3 

6 

12AWG 

C182 101 TURBINE CONTROL PANEL 

3 

12 

12AWG 

C257 101 TURBINE CONTROL PANEL 

3 

12 

12AWG 

CG1032 901 CUSTOMER GROUND GRID 

4 

1 

1/0AWG 

GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 21 + (GR0730) 

233 JB020A TURBINE OFF BASE RACK LOW LEVEL 

cable I to 
C039 URBINE CONTROL PANEL 
C041 URBINE ':ONTROL PANEL 
C200 URBINE' ONTROL PANEL 
190 U8TOMER GROUND GRID 

234 JB020B TURBINE OFF BASE RACK LOW LEVEL 
(Stamp comment
#41 dborgstadt
12/19/2010 12:55:12 PM
blank)
lev 

1S 

lS 

lS 

4 

#cnd 

18 

18 

36 

1 
aauae 

18AWG 

18AWG 

18AWG 

1/0AWG 

cable I to 

lev 

#cnd 

QauQe 

751 FLAME I MODULE~ARY 

38 

8 

18AWG

CO~ 

COO 

752 FLAME DETEC ClR I MODULE ,y 

3S 

8 

18AWG 

C038 

URBINE :ONTROL PANEL 

1 

36 

18AWG 

227 i GAS MONI DRC17 

2 

9 

lOAWG 

190 U8TOMER GROUND GRID 

4 

1 

1/0AWG 

252 WATER WASH SKID 


SIZE 

CAGE CODE 

DWGNO

• GENERAL ELECTRIC COMPANY 
~~=G=E==p=o=~=e=r=Ge_n_e_ra_t_ion ________ ~~ 

377A4380 

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SHEET 

DOCUMENT SERVICES 01-07-26 

22 

(GR0730) 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:07 PM
blank)
254 CUSTOMER DEVICES--PANELS 

cable I to lev #cnd aauae 
C401 183 <Y ORMER 4 
C410A 334 PEEC MOlaR aNTRaL 3 2 'AWG 
C410B 334 PEEC MOl aR' aNTROL 3 2 'AWG 
C420A 102 GENERA-OR aNTROL PANEL 3 4 11'AWG 
C420B 102 GENERATOR CONTROL PANEL 3 4 10AWG 
C426 08 I\IJXIL I\RY RELI\Y PI\NEL 1 12 181\WG 
C426A 108 A I 'RELAY PANEL 1 3 18AWG 
C549 )2 , PANEL 1 18 18AWG 
C549A 108 I ~Y RELAY PANEL 1 18 18AWG 
CbbUA 101 UK~INc CUN I KUL ~ANcL 18 l'LAWG 
C550B 10 URBINE ONTROL PANEL 3 19 12AWG 
C550C URBINE' , PANEL 3 19 12AWG 
C550D 101 URBINE' OL~ 3 19 ~~~Cbb1A 101 UK~INc CUN I KUL 1'L 
;51B 'A 
;51 
;53A 'A 
Cbb4 JA 
C610A 102 GENERA-OR ONTROL PANEL 3 12 12AWG 
C610B 108 I ~Y RELAY PANEL 3 2 12AWG 
C610C 108 ' RELAY PANEL 3 12 12AWG 
CblOU 08 AUXILIAKY KcLA' ~ANcL 1'L 1'L AWG 
I _AY 'A 
A WPA 
I IY 
I 
I \Y 
)N'
ANEL W 
'ANEL W( 
I ,AW( 
IA INPANEL 
,AWl 
C W A I ELAY 
~C IA G 'IAON--
R 
JM=H LJ 
257 JB037 PERFORMANCE MONITORING LOW LEVEL 

cable to lev #cnd au e 
C678 101 TURBINE CONTROL PANEL 1 18 18AWG 

280 GENERATOR NEUTRAL ACCESSORY COMPARTMENT GNAC 

cable to lev #cnd au e 
CG1051 901 CUSTOMER GROUND GRID 4 2 4/0 AWG 

SIZE 

CAGE CODE 

DWGNO

• GENERAL ELECTRIC COMPANY 
~~=G=E==p=o=~=e=r=Ge_n_e_ra_t_ion ________ ~~ 

377A4380 

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SHEET 

DOCUMENT SERVICES 01-07-26 

23 

(GR0730) 



.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:55:03 PM
blank)
SOZEAIUWj,'7A4380 ~4 I"EVc I + 
283 FIRE PROTECTION DEVICES 
~ I to I lev I #cnd I aauae I 
90 CUS10MER lGRIC I 4 I 2 I 4/0 AWG I 
284 FIRE PROTECTION PANEL 
~ 
,. #c ,d ,allae 
77A A lASE FP W 
77A A \SE FP W 
miNE NEL W( 
~~~ LE W( 
339 LEVI W 
C874 339 JB298 PEECC LEVEl 3 4 3 'AWG 
325 JB163 GENERATOR COMPARTMENT LOW LEVEL 
I cable Ito I lev I #cnd I gauge I 
C145 208 VIBRATION MONITOR PANEL I 1 I 18 I 18AWG I 
329 CRANKING MOTOR TRANSFORMER 
cable to lev #cnd gauge 
C598 201 LIMIT AMP 5 3 
C745A 146 METALCLAD SWITCHGEAR 5 3 
C745B 183 AUXILIARY POWER TRANSFORMER 5 3 
333 PACKAGED ELECTRICAL-ELECTRONIC CONTROL CENTER-PEECC 
cable to I lev I #cnd I Qauae I 
CG1008 901 CUSTOMER GROUND GRID 4 2 4/0AWG 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 24 + (GR0730) 

(Stamp comment
#41 dborgstadt
12/19/2010 12:55:00 PM
blank)
334 PEECC MOTOR CONTROL CENTER 
cable I to lev #cnd 
C012 392 JB004 A BASE LEVEl. 4 4 
C013e 392 JB004 A BASE LEVEI.4 4 3 
C02? 18 ACe . BASE MOTORS 4 3 
C028 392 JB004 BASE LEVEl. 4 4 3 
C055A 381 JB021A TURBINE OFF BASE RACK LEVEL 4 4 3 
C055B 381 JB0211\ URBINE ClFF BI\SE Rl\CK LEVEL 4 4 3 
C059 133 JB005e OR COMPI JT _EVEL 4 4 3 
CO? 128 EXHAUS-' FRAME BLOWER 88TK-1 4 3 
C072 129 iT FRAME 88TK-2 4 3 
aauae 
4AWG 
'AWG 
2AWG 
8AWG 
8AWG 
81\WG 
'AWG 
f-_C",:lO;;/I/Oc---+~-;; Mc I ALCLALJ I ;cAK 4 8 AWG 
C102 12 JB004 ::JRY BASE LEVEl 4 4 3 8 AWG 
f--C~2:?-5--+*12 JB004 ACCESSORY BASE LEVEl. 4 4 5 'AWG 
C149 ~JB131 ;ASFUELMODULE ~~4~__________________________~4~~3~f-~81~N\~WCG~~ 
C199 1« UK81Nc KUUr MUUN I cLJ LJEVICES 4 8 AWG 
-ALe I ;EAR 6 AWG 
)4 ESSORY BASE LEVEl. 4 6 AWG 
I . AF ::JL DOOR LIGHTING 
I 
,:; 
C406 182 MAIN' ~(STEPUP) 4 3 
C40? 182 MAINTRANSF~~~(~s·trE~"P~U~p1)==============================t=4~~=~3t~~======~
C408 I 00 fA! ' ONE 4 3 
C409A 18L MAIN I KAI ::; I c~ U~) L 
f-~-'.C09:c;-B--+~~~""T~' ,NSFOF ,p UP)
OA _S 
OB _S 
XI 
JA coe I 
JA coe I 
JA cae I ; WA 
DL 
DL 
38 JB09aA :OOLING 
l3 ~Y 
_EVEL 4 
~ER 
f-""*,~__~l+---i3A"",,~IIAI~Y 
.IMIT AII~ 
~ER 
C672 
C809 
C81? 
176 UBE OIL DE (TURBINE) 
144' JB13' GAS FUEL LEVEL 4 
44' JB131 GAS FUEL MODULE LEVEL 4 
335 BUS DUCT 
cable 
C080 
CG1059 
to 
146 METALCLAD SWITCHGEAR 
901 CUSTOMER GROUND GRID 
338 CUSTOMER 480V SUPPLY 
cable to 
C415 183 AUXILIARY POWER TRANSFORMER 
GENERAL ELECTRIC COMPANY SIZE•~~=G=E==p=o=~=e=r=G__e_n_e_ra_t_io__n ________ ~~ 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED DOCUMENT SERVICES 01-07-26 
CAGE CODE DWGNO 
377A4380 
4 
4 
4 
3 
3 
3 
lev #cnd 
3 3 
4 2 
lev #cnd 
4 3 
SHEET 25 
au e 
12AWG 
4/01\WG 
au e 
(GR0730) 



(Stamp comment
#41 dborgstadt
12/19/2010 12:54:57 PM
blank)
339 JB298 PEECC LEVEL 3 

cable 
C151 
C190 
C192 
C199A 
C216 
C217 
C219 
C249 
C270 
C01 
C532 
C544 
C607A 
Cb/LA 
C7; 
C80 
C8 
ce 
I to lev #cnd aauae 
JB002 A JR" BASE _EVEL 3 12 'AWG 
128 . FRAME 88TK-1 3 2 'AWG 
129 EXHAUS-' FRAME BLOWER 88TK-2 3 2 'AWG 
122 URBINE ROOF MOUNTED I 3 2 11' AWG 
363 JB130 GAS FUEL 3 3 12 AWG 
353 JB130 GAS FUEL 3 2 'AWG 
136 JB005B GENERA' OR' LEVEL 3 3 2 12 AWG 
I 581 JBOO5N GEN. NEU rRAI IES C OMP. LEVEL 3 3 3 'AWG 
115 JB002 JRY BASE LEVEL 3 3 12 12 AWG 
1449 J80/8 JK8. AIK INLe HL I eK <eN I b AVVG 
1428 JB090 OOLING WATER MODULE LEVEL 3 3 2 12 AWG 
1428 JB090 OOLING WATER MODULE LEVEL 3 3 2 'AWG 
225 RELATIVE HUM IDI'-Y ~'i2cR,,----_____-----___--
t_f---3f---;3:i-+---+11;2~.A';iCi;W*-'--j 
lIb U8e '-'IL LJeMl:oi I eK (TURBINe) L 'AWG 
I 'SKI[ LEVEL 3 
, FUEL MC ULE LEVEL 4 
, FUEL MC ULE LEVEL 4 
IN ~ANeL .AI 
C872 284 FI RE ON PANEl 
ON PANEL 
3 12 12AWG 
'AWGC874 284 FIRE 4 3 
348 JB077A ACCESSORY BASE FP 

gauge

cable 

to 

lev 

#cnd 

C135 284 FIRE PROTECTION PANEL 

25 

18 

18AWG 

C136 284 FIRE PROTECTION PANEL 

2S 

18 

18AWG 

363 JB130 GAS FUEL MODULE 

cable 

C006 

C014 

C022 

C096 

C216 

C217 

C285 

to 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
227 HAZARDOUS GAS MONITOR 
101 TURBINE CONTROL PANEL 
339 JB298 PEECC LEVEL 3 
339 JB290 PEECC LEVEL 3 
101 TURBINE CONTROL PANEL 

lev 

1 

3 

2 

1 

3 

3 

1S 

#cnd 

36 

37 

9 

36 

3 

2 

6 

Qauae 

18AWG 

12AWG 

18AWG 

18AWG 

12AWG 

10AWG 

18AWG 

381 JB021A TURBINE OFF BASE RACK LEVEL 4 


SIZE 

CAGE CODE 

DWGNO

• GENERAL ELECTRIC COMPANY 
~~=G=E==p=o=~=e=r=Ge_n_e_ra_t_ion ________ ~~ 

377A4380 

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SHEET 

DOCUMENT SERVICES 01-07-26 

26 

(GR0730) 


SOZEAIUWj,'7A4380 I~ I"EVc I 

+ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:54 PM
blank)
387 JB020G TURBINE COMPARTMENT LOW LEVEL 

cable 
C073 
C074 
C473 
C474 
to 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
lev 
1S 
1S 
1 
1 
#cnd 
36 
36 
2 
2 
Qauae 
18AWG 
18AWG 
18AWG 
18AWG 

390 JB034 TURBINE ROOF LOW LEVEL 

cable to I lev I #cnd I QauQe I 
C201 101 TURBINE CONTROL PANEL I 1 I 8 I 18AWG I 
392 JBOO4 ACCESSORY BASE LEVEL 4 

cable to lev #cnd QauQe 
C012 334 PEECC MOTOR CONTROL CENTER 4 3 4AWG 
C013C 334 PEECC MOTOR CONTROL CENTER 4 3 10AWG 
C028 334 PEECC MOTOR CONTROL CENTER 4 3 8AWG 
C102 334 PEECC MOTOR CONTROL CENTER 4 3 8AWG 
C125 334 PEECC MOTOR CONTROL CENTER 4 5 10AWG 
C251 334 PEECC MOTOR CONTROL CENTER 4 3 6AWG 

428 JB090 COOLING WATER MODULE LEVEL 3 

cable 
CoJ1 
C532 
C544 
Ito 
UK~INe 
339 JB298 PEECC 
339 JB298 PEECC 
OL ~ANeL 
LEVEl 3 
LEVEl 3 
lev 
3 
3 
#cnd 
2 
2 
gauge 
'LAWG 
12AWG 
'AWG .. 438 JB090A COOLING WATER MODULE LEVEL4 



~ 

I IE #cnd gauge 
134 PEEC OL 
134 PEEC OL 
134 PEECC MOl OR CONTROL C 
C537 334 PEEC M010R :ONTROL CENTER 4 3 
C538 334 PEEC MOl OR' ONTROL CENTER 4 3 
441 JB131 GAS FUEL MODULE LEVEL 4 

,auge

cable 

to 

IE 

#cnd 

;149 334 PEEC OL 

I~ 

C80"A 

JJ" J~L"8 ~eeCl LeVe' 

C817 

334 PEEC M010R :ONTROL CENTER 

4 

3 

'AWG 

,AWG

CB17A 339 JB298 PEEC LEVEl 3 

3 

2 

GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 27 
+ (GR0730) 


SOZEAIUWj,'7A4380 1~8 I"EVc I + 
447 INLET HEATING CONTROL VALVE 
449 JB078 TURB. AIR INLET FILTER COMPARTMENT 
cable to I lev I #cnd I Qauae I 
C512 101 TURBINE CONTROL PANEL I 3 I 7 I 12AWG I 
C515 339 JB298 PEECC LEVEL 3 I 3 I 3 I 6AWG I 
455 JB297 AIR PROCESS SKID LEVEL 3 
I cable Ito I lev I #cnd I gauge I 
C725 339 JB298 PEECC LEVEL 3 I 3 I 3 I 12AWG I 
C727 101 TURBINE CONTROL PANEL I 3 I 6 I 12AWG I 
456 JB010 WATER WASH SKID LEVEL 3 
514 CUSTOMER SWITCHGEAR 
I cable Ito I lev I #cnd I gauge I 
C480 334 PEECC MOTOR CONTROL CENTER I 3 I 3 I 12AWG I 
C481 334 PEECC MOTOR CONTROL CENTER I 3 I 2 I 10AWG I 
562 STATIC VOLTAGE REGULATOR--EX2000R 
563 JB386 GAS SCRUBBER LEVEL 3 
I cable Ito I lev I #cnd I gauge I 
C819 101 TURBINE CONTROL PANEL I 3 I 19 I 12AWG I 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 28 
.. ~ 

+ (GR0730) 

cable to 
(Stamp comment
#41 dborgstadt
12/19/2010 12:54:51 PM
blank)
lev #cnd Qauae 
CS16A 101 TURBINE CONTROL PANEL 3 2 12AWG 
CS17A 101 TURBINE CONTROL PANEL 1 2 18AWG 
CS17B 101 TURBINE CONTROL PANEL 1 2 18AWG 
CS17D 101 TURBINE CONTROL PANEL 1 2 18AWG 
CS17E 101 TURBINE CONTROL PANEL 1 2 18AWG 

cable 
C667-1 
C667-2 
C667-3 
C667-4 
to 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
101 TURBINE CONTROL PANEL 
lev 
3 
3 
3 
3 
#cnd 
12 
12 
12 
12 
gauge 
12AWG 
12AWG 
12AWG 
12AWG 

cable to lev #cnd QauQe 
CD94B 135 JBDDSA GENERATOR COMPARTMENT LOW LEVEL 1 8 18AWG 
C123 
C148 
136 JBOOSB GENERATOR COMPARTMENT 
146 METALCLAD SWITCHGEAR 
LEVEL 3 3 
3 
6 
4 
10AWG 
1DAWG 


.. ~ 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:47 PM
blank)
SOZEAIUWj,'7A4380 1~9 I"EVc I + 
581 JB005N GEN. NEUTRAL ACCESSORIES COMPo LEVEL 3 
cable to lev #cnd Qauae 
C236A 102 GENERATOR CONTROL PANEL 3 12 10AWG 
C236B 102 GENERATOR CONTROL PANEL 3 12 10AWG 
C249 339 JB298 PEECC LEVEL 3 3 3 10AWG 
611 INLET HEATING ISOLATION VALVE 
cable to I lev I #cnd I gauge I 
C516E 101 TURBINE CONTROL PANEL I 3 I 2 I 12AWG I 
622 FUEL GAS HEATER CONTROL PANEL 
cable I to lev #cnd QauQe 
C4 183 A ~y POWER ORMER 4 3 
C413 753 J~;ASHEA~3 1 6 18AWC 
C414 /,,3 Je, GA:oi HcA I I I 3 'LAWG 
C414A 10 URBINE ONTROL PANEL 3 7 12AWG 
742 SITE LIGHTS 
cable to I lev I #cnd I gauge I 
C403 334 PEECC MOTOR CONTROL CENTER I 4 I 3 I I 
751 FLAME DETECTOR INTERFACE MODULE PRIMARY 
cable to I lev I #cnd I gauge I 
C009A 234 JB020B TURBINE OFF BASE RACK LOW LEVEL I 3S I 8 I 18AWG I 
752 FLAME DETECTOR INTERFACE MODULE SECONDARY 
cable to I lev I #cnd I gauge I 
COO9B 234 JB020B TURBINE OFF BASE RACK LOW LEVEL I 3S I 8 I 18AWG I 
753 JB309 FUEL GAS HEATING SKID LEVEL 3 
GENERAL ELECTRIC COMPANY SIZE CAGE CODE DWGNO•GE Power Generation A 377A4380 
DRAWN 
DAVID H MATTICE 01-07-26 
ISSUED SCALE 
NONEI SHEET 
DOCUMENT SERVICES 01-07-26 29 + (GR0730) 
cable 
C413 
C414 
to 
622 FUEL GAS HEATER CONTROL PANEL 
622 FUEL GAS HEATER CONTROL PANEL 
lev 
1 
3 
#cnd 
6 
3 
gauge 
18AWG 
12AWG 


901 CUSTOMER GROUND GRID 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:43 PM
blank)
cable I to lev #cnd aauae 
CG1007 254 CUSTOMER OEVI 4 1 'AWG 
333PACMGEIC_ECTRICAL-EL ; CONTROL 4 2AWG 
CG103-230 JB019A INEOFFB~~RA~C;2-KTL~EV/IE~13~____________________-+~4T4~I~~~'AT.T.W~CG 

23' JB019B INE OFF B~RACK LEVEl 3 4 1 'AWG 
CG1033 I 233 JB020A TURBINE OFF BASE RACK LOW LEVEL 4 1 0 AWG 
234 JB020B URBINE OFF BI\SE RACK LOW LEVEL 4 1 I\WG 

CG1038 38' JB021A URBINE OFF BASE RACK LEVEL 4 4 1 'AWG 
CG105 280 GNAC 4 2 'AWG 
( 335 BUS DUCT 4 2 4/0 AWG 
CG80L bl UK~INc AIK INLc rill cK 4 L 10 AWG 

~~6~~'8~2~M~~'AIN~T~RA\~'NSF~CO~RM~ERI~(!(~S-rE~PU~p)______________________________~4~~2~~~A~WIG~ 
:G90 146 METALC LAD SWI ;HGEAR 4 2 AWG 
CG9l' 161 COOLING WATER #1 4 /0 AWl 
CG814 lL' UK~INc ~A~c 4 L 10 AWG 
1915 -BA,E AV 
1920 AV 

~~AS I\:I~KI~MO~EIT========================~+=~~~~:~ 


:G929 172 AIR ,SKII 4 2 AWG 
:G931 183 I POWER ORMER 4 2 AWG 
:G933 20 LIMIT AMP 4 2 AWG 
CG8b4 be GA~ 4 L 10 AWG 
:G964 128 -FRAME 88TK-1 4 2 AWG 
:G965 129 EXHAUST FRAME BLOWER 88TK-2 4 2 AWG 
:G983 283 FI RE )N DEVICES 4 2 AWG 

938 CEMS SYSTEM 

cable to lev #cnd au e 

C404 334 PEECC MOTOR CONTROL CENTER 4 3 

939 UNIT AREA OUTDOOR LIGHTING 

cable to lev #cnd au e 

C402 334 PEECC MOTOR CONTROL CENTER 4 3 

SIZE 

CAGE CODE 

DWGNO

• GENERAL ELECTRIC COMPANY 
~~=G=E==p=O=~=e=r=Ge_n_e_ra_t_ion ________ ~~ 

377A4380 

DRAWN 

DAVID H MATTICE 01-07-26 

ISSUED 

SHEET 

DOCUMENT SERVICES 01-07-26 

30 

(GR0730) 


Notes 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:36 PM
blank)
1 "C" PREFIX INDICATES CABLE SUPPLIED BY OTHERS THAN GE-GAS TURBINE DIVISION. CONT 

2"C" PREFIX CABLES TO BE RATED NOT LESS THAN 90 DEG. C. 

3CABLE GLANDS/STRESS RELIEFS FOR CONNECTING CABLES AT JUNCTION BOXES/DEVICES A 

4BEND RADIUS -BENDS SHALL BE SO MADE THAT CABLE WILL NOT BE DAMAGED. AND RADIU 

5CABLES SUPPLIED BY OTHERS THAT ARE SHOWN ON THIS DWG. ARE ONLY FOR THOSE WHI 

6MAKEUP OF "C" PREFIX CABLES ARE SUGGESTED TO ENSURE SUFFICIENT CONDUCTOR COU 

7"C" PREFIX CABLES FOR LEVEL 4 AND LEVEL 5 POWER SUPPLY ARE SIZED BY OTHERS. 

8SEE OUTLINE. GAS TURBINE PACKAGE CONNECTION -ELECTRICAL DIAG .. M.L. ITEM 0301 FOR 

9CABLE TO BE INSTALLED WITH ADEQUATE SEPARATION BETWEEN DIFFERENT LEVELS AND I 

10GROUND CABLES ARE TO BE SUPPLIED ON ALL EQUIPMENT. TWO CABLE CONNECTIONS AR 

11 ONE CABLE REQUIRED PER SITE. 

12CABLE REQUIRED FOR UNITS 1 & 3 ONLY. 

13CABLE REQUIRED FOR UNITS 2 & 4 ONLY. 

14FOR ADDITIONAL COMMUNICATION CABLES SEE M.L. ITEM 4108. 

15 REFER TO DWG. 358B1 001 FOR CABLE ROUTING. 
cable DO IDe LOC DES(D1 IDe LOC DES(NO CONDGAUGE CONFIG LEV 
C001 101 TURBINE (136 JB005B GI19 12AWG 1 CABLE 3 
C006 101 TURBINE (363 JB130 GAi36 18AWG 1 CABLE-1i1 
C009A 234 JB020B TL751 FLAME DE8 18AWG 1 CABLE-43S 
C009B 234 JB020B TL752 FLAME DE8 18AWG 1 CABLE-43S 
C012 334 PEECC ~392 JB004 AC3 4AWG 1 CABLE 4 
C013C 334 PEECC ~392 JB004 AC3 10AWG 1 CABLE 4 
C014 101 TURBINE (363 JB130 GAi37 12AWG 1 CABLE 3 
C017 101 TURBINE (135 JB005A GI36 18AWG 1 CABLE-1i1 
C018 101 TURBINE (135 JB005A GI18 18AWG 1 CABLE-91S 
C022 227 HAZARDOl363 JB130 GAi9 18AWG 1 CABLE-32 
C027 118 ACCESSOl334 PEECC ~3 2AWG 1 CABLE 4 
C028 334 PEECC ~392 JB004 AC3 8AWG 1 CABLE 4 
C037 101 TURBINE (115 JB002 AC(37 12AWG 1 CABLE 3 
C038 101 TURBINE (234 JB020B TL36 18AWG 1 CABLE-1i1 
C039 101 TURBINE (233 JB020A TL18 18AWG 1 CABLE-91S 
C041 101 TURBINE (233 JB020A TL18 18AWG 1 CABLE-91S 
C042 101 TURBINE (230 JB019A TL19 12AWG 1 CABLE 3 
C049 102 GENERAT(146 METALCLt37 12AWG 1 CABLE 3 
C055A 334 PEECC ~381 JB021A TL3 8AWG 1 CABLE 4 
C055B 334 PEECC ~381 JB021A TL3 8AWG 1 CABLE 4 
C059 133 JB005C GI334 PEECC ~3 10AWG 1 CABLE 4 
C071 128 EXHAUST 334 PEECC ~3 SIZED BY (4 
C072 129 EXHAUST 334 PEECC ~3 SIZED BY (4 
C073 101 TURBINE (387 JB020G Tl36 18AWG 1 CABLE-1i1S 
C074 101 TURBINE (387 JB020G Tl36 18AWG 1 CABLE-1i1S 
C076 101 TURBINE (135 JB005A GI18 18AWG 1 CABLE-91 
C077 146 METALCLfl334 PEECC ~3 8AWG 1 CABLE 4 
C080 146 METALCLfl335 BUS DUCT3 12AWG 1 CABLE 3 
C083 102 GENERAT(146 METALCLt12 10AWG 1 CABLE 3 
C094B 135 JB005A GI562 STATIC V(8 18AWG 1 CABLE-41 
C096 101 TURBINE (363 JB130 GAi36 18AWG 1 CABLE-1i1 
C102 334 PEECC ~392 JB004 AC3 8AWG 1 CABLE 4 
C117A 125 JB055 TUF208 VIBRATlm18 18AWG 1 CABLE-61 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:32 PM
blank)
C117B 126 JB056 TUF208 VIBRATlm18 18AWG 1 CABLE-61 
C117C 127 JB085 LOJ208 VIBRATlm9 18AWG 1 CABLE-31 
C123 136 JB005B GI562 STATIC V(6 10AWG 1 CABLE 3 
C125 334 PEECC ~392 JB004 AC5 10AWG 1 CABLE 4 
C128 101 TURBINE (231 JB019B Tl6 12 AWG 1 CABLE 3 
C135 284 FIRE PR0l348 JB077A A(18 18 AWG 1 CABLE-92S 
C136 284 FIRE PR0l348 JB077A A(18 18 AWG 1 CABLE-92S 
C143 133 JB005C GI334 PEECC ~3 12 AWG 1 CABLE 4 
C145 208 VIBRATlm325 JB163 GEI18 18AWG 1 CABLE-61 
C148 146 METALCLfl562 STATIC V(4 10AWG 1 CABLE 3 
C149 334 PEECC M41 JB131 GAi3 8 AWG 1 CABLE 4 
C161 115 JB002 AC(339 JB298 PEE12 10AWG 1 CABLE 3 
C171 227 HAZARDOl234 JB020B Tl9 18 AWG 1 CABLE-32 
C172 114 JB001 AC(201 LIMIT AMP18 18AWG 1 CABLE-61 
C182 101 TURBINE (231 JB019B Tl12 12 AWG 1 CABLE 3 
C190 128 EXHAUST 339 JB298 PEE2 10AWG 1 CABLE 3 
C191 101 TURBINE (128 EXHAUST 3 12 AWG 1 CABLE 3 
C192 129 EXHAUST 339 JB298 PEE2 10AWG 1 CABLE 3 
C193 101 TURBINE (129 EXHAUST 3 12 AWG 1 CABLE 3 
C199 122 TURBINE F334 PEECC ~3 8 AWG 1 CABLE 4 
C199A 122 TURBINE F339 JB298 PEE2 10AWG 1 CABLE 3 
C200 101 TURBINE (233 JB020A Tl36 18 AWG 1 CABLE-1i1 S 
C201 101 TURBINE (390 JB034 TUF8 18AWG 1 CABLE-41 
C216 339 JB298 PEE363 JB130 GAi3 12 AWG 1 CABLE 3 
C217 339 JB298 PEE363 JB130 GAi2 10AWG 1 CABLE 3 
C219 136 JB005B GI339 JB298 PEE12 12 AWG 1 CABLE 3 
C235A 102 GENERAT(146 METALCLt12 10AWG 1 CABLE 3 
C235B 102 GENERAT(146 METALCLt12 10AWG 1 CABLE 3 
C235C 108 AUXILlAR'V146 METALCLt12 10AWG 1 CABLE 3 
C236A 102 GENERAT(581 JB005N GI12 10AWG 1 CABLE 3 
C236B 102 GENERAT(581 JB005N GI12 10AWG 1 CABLE 3 
C236C 102 GENERAT(146 METALCLt12 10AWG 1 CABLE 3 
C237 146 METALCLfl334 PEECC ~2 6 AWG SINGLE C(4 
C249 339 JB298 PEE581 JB005N GI3 10AWG 1 CABLE 3 
C251 334 PEECC ~392 JB004 AC3 6 AWG 1 CABLE 4 
C256 101 TURBINE (230 JB019A Tl3 10AWG 1 CABLE 3 
C257 101 TURBINE (231 JB019B Tl12 12 AWG 1 CABLE 3 
C270 115 JB002 AC(339 JB298 PEE12 12 AWG 1 CABLE 3 
C285 101 TURBINE (363 JB130 GAi6 18AWG 1CABLE-31S 
C401 183 AUXILlAR'V254 CUSTOME3 SIZED BY (4 
C402 334 PEECC ~939 UNIT AREJ3 SIZED BY (4 
C403 334 PEECC ~742 SITE LlGH"3 SIZED BY (4 
C404 334 PEECC ~938 CEMS SYS3 SIZED BY (4 
C406 182 MAIN TRAt334 PEECC ~3 SIZED BY (4 
C407 182 MAIN TRAt334 PEECC ~3 SIZED BY (4 
C408 001 WELDING 334 PEECC ~3 SIZED BY (4 
C409A 182 MAIN TRAt334 PEECC ~2 10AWG 1 CABLE 3 
C409B 182 MAIN TRAt334 PEECC ~2 10AWG 1 CABLE 3 
C410A 254 CUSTOME334 PEECC ~2 10AWG 1 CABLE 3 
C410B 254 CUSTOME334 PEECC ~2 10AWG 1 CABLE 3 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:29 PM
blank)
C411 183 AUXILlAR'V622 FUEL GAS3 SIZED BY (4 
C413 622 FUEL GAS 753 JB309 FUE6 18AWG 1 CABLE-31 
C414 622 FUEL GAS 753 JB309 FUE3 12 AWG 1 CABLE 3 
C414A 101 TURBINE (622 FUEL GAS7 12 AWG 1 CABLE 3 
C415 183 AUXILlAR'V338 CUSTOME3 SIZED BY (4 
C417A 102 GENERAT(102 GENERAT(12 10AWG 1 CABLE 3 
C418A 102 GENERAT(102 GENERAT(12 10AWG 1 CABLE 3 
C420A 102 GENERAT(254 CUSTOME4 10AWG 1 CABLE 3 
C420B 102 GENERAT(254 CUSTOME4 10AWG 1 CABLE 3 
C421 108 AUXILlAR'V108 AUXILlAR'I'12 12 AWG 1 CABLE 3 
C421 A 108 AUXILlAR'V108 AUXILlAR'I'12 12 AWG 1 CABLE 3 
C421B 108 AUXILlAR'V108 AUXILlAR'I'12 12 AWG 1 CABLE 3 
C421C 108 AUXILlAR'V108 AUXILlAR'I'12 12 AWG 1 CABLE 3 
C422 108 AUXILlAR'V108 AUXILlAR'I'6 12 AWG 1 CABLE 3 
C422A 108 AUXILlAR'V108 AUXILlAR'I'6 12 AWG 1 CABLE 3 
C426 108 AUXILlAR'V254 CUSTOME12 18AWG 1 CABLE-61 
C426A 108 AUXILlAR'V254 CUSTOME3 18AWG 1 CABLE-11 
C428 101 TURBINE (146 METALCLt6 12 AWG 1 CABLE 3 
C473 101 TURBINE (387 JB020G Tl2 18 AWG 1 CABLE-11 
C474 101 TURBINE (387 JB020G Tl2 18 AWG 1 CABLE-11 
C512 101 TURBINE (449 JB078 TUF7 12 AWG 1 CABLE 3 
C513A 101 TURBINE (157 TURBINEJ2 18AWG 1 CABLE-11S 
C513B 101 TURBINE (157 TURBINEJ2 18AWG 1 CABLE-11S 
C513C 101 TURBINE (157 TURBINEJ2 18AWG 1 CABLE-11S 
C515 339 JB298 PEE449 JB078 TUF3 6 AWG 1 CABLE 3 
C516A 101 TURBINE (447 INLET HEA2 12 AWG 1 CABLE 3 
C516E 101 TURBINE (611 INLET HEA2 12 AWG 1 CABLE 3 
C517A 101 TURBINE (447 INLET HEA2 18 AWG 1 CABLE-11 
C517B 101 TURBINE (447 INLET HEA2 18 AWG 1 CABLE-11 
C517D 101 TURBINE (447 INLET HEA2 18 AWG 1 CABLE-11 
C517E 101 TURBINE (447 INLET HEA2 18 AWG 1 CABLE-11 
C531 101 TURBINE (428 JB090 COl6 12 AWG 1 CABLE 3 
C532 339 JB298 PEE428 JB090 COl12 12 AWG 1 CABLE 3 
C533 334 PEECC M38 JB090A C(3 SIZED BY (4 
C534 334 PEECC M38 JB090A C(3 SIZED BY (4 
C535 334 PEECC M38 JB090A C(3 SIZED BY (4 
C537 334 PEECC M38 JB090A C(3 SIZED BY (4 
C538 334 PEECC M38 JB090A C(3 SIZED BY (4 
C544 339 JB298 PEE428 JB090 COl12 10AWG 1 CABLE 3 
C549 102 GENERAT(254 CUSTOME18 18AWG 1 CABLE-61 
C549A 108 AUXILlAR'V254 CUSTOME18 18AWG 1 CABLE-61 
C550A 101 TURBINE (254 CUSTOME19 12 AWG 1 CABLE 3 
C550B 101 TURBINE (254 CUSTOME19 12 AWG 1 CABLE 3 
C550C 101 TURBINE (254 CUSTOME19 12 AWG 1 CABLE 3 
C550D 101 TURBINE (254 CUSTOME19 12 AWG 1 CABLE 3 
C551A 101 TURBINE (254 CUSTOME12 12 AWG 1 CABLE 3 
C551B 101 TURBINE (254 CUSTOME12 12 AWG 1 CABLE 3 
C551C 101 TURBINE (254 CUSTOME12 12 AWG 1 CABLE 3 
C553A 101 TURBINE (254 CUSTOME18 18AWG 1 CABLE-91 
C553B 101 TURBINE (254 CUSTOME18 18AWG 1 CABLE-91 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:26 PM
blank)
C554 101 TURBINE (254 CUSTOME4 12 AWG 1 CABLE 3 
C575 149 CRANKING201 LIMIT AMP3 SIZED BY(5 
C583 183 AUXILlAR'V334 PEECC ~6 2 PER PH.4 
C584 183 AUXILlAR'V334 PEECC ~6 2 PER PH.4 
C590 101 TURBINE (201 LIMIT AMP6 12 AWG 1 CABLE 3 
C591 108 AUXILlAR'V183 AUXILlAR'I'2 10AWG 1 CABLE 3 
C593 108 AUXILlAR'V183 AUXILlAR'I'4 10AWG 1 CABLE 3 
C596 201 LIMIT AMP334 PEECC ~2 10AWG 1 CABLE 3 
C598 201 LIMIT AMP329 CRANKING3 SIZED BY(5 
C607 101 TURBINE (225 RELATIVE 2 18 AWG 1 CABLE-11 
C607A 225 RELATIVE 339 JB298 PEE3 12 AWG 1 CABLE 3 
C610A 102 GENERAT(254 CUSTOME12 12 AWG 1 CABLE 3 
C610B 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610C 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610D 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610E 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610F 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610FA 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610FB 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610FC 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610H 102 GENERAT(254 CUSTOME12 12 AWG 1 CABLE 3 
C610HA 102 GENERAT(254 CUSTOME12 12 AWG 1 CABLE 3 
C610J 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C610V 102 GENERAT(254 CUSTOME12 12 AWG 1 CABLE 3 
C610W 108 AUXILlAR'V254 CUSTOME12 12 AWG 1 CABLE 3 
C611 102 GENERAT(254 CUSTOME12 12 AWG 1 CABLE 3 
C611A 102 GENERAT(254 CUSTOME6 12 AWG 1 CABLE 3 
C615D 101 TURBINE (156 FUEL GAS2 18 AWG 1 CABLE-11 
C667-1 101 TURBINE (456 JB010 WA12 12 AWG 1 CABLE 3 
C667-2 101 TURBINE (456 JB010 WA12 12 AWG 1 CABLE 3 
C667-3 101 TURBINE (456 JB010 WA12 12 AWG 1 CABLE 3 
C667-4 101 TURBINE (456 JB010 WA12 12 AWG 1 CABLE 3 
C669 183 AUXILlAR'V252 WATER W,3 SIZED BY (4 
C671 101 TURBINE (176 LUBE OIL 13 12 AWG 1 CABLE 3 
C672 176 LUBE OIL [334 PEECC ~3 SIZED BY (4 
C672A 176 LUBE OIL [339 JB298 PEE2 10AWG 1 CABLE 3 
C678 101 TURBINE (257 JB037 PE18 18AWG 1 CABLE-91 
C725 339 JB298 PEE455 JB297 AIR3 12 AWG 1 CABLE 3 
C727 101 TURBINE (455 JB297 AIR6 12 AWG 1 CABLE 3 
C743 102 GENERAT(201 LIMIT AMP2 10AWG 1 CABLE 3 
C745A 146 METALCLfl329 CRANKING3 SIZED BY(5 
C745B 183 AUXILlAR'V329 CRANKING3 SIZED BY(5 
C776 136 JB005B GI151 JB215 GEI5 12 AWG 1 CABLE 3 
C777 136 JB005B GI151 JB215 GEI2 12 AWG 1 CABLE 3 
C809 334 PEECC M41 JB131 GAi3 10AWG 1 CABLE 4 
C809A 339 JB298 PEE441 JB131 GAi2 10AWG 1 CABLE 3 
C817 334 PEECC M41 JB131 GAi3 10AWG 1 CABLE 4 
C817A 339 JB298 PEE441 JB131 GAi2 10AWG 1 CABLE 3 
C819 101 TURBINE (563 JB386 GAi19 12 AWG 1 CABLE 3 
C849 201 LIMIT AMP339 JB298 PEE3 10AWG 1 CABLE 3 



(Stamp comment
#41 dborgstadt
12/19/2010 12:54:22 PM
blank)
C870 101 TURBINE (284 FIRE PR0112 12AWG 1 CABLE 3 
C871 284 FIRE PR01339 JB298 PEE3 12AWG 1 CABLE 3 
C872 284 FIRE PR01339 JB298 PEE12 12AWG 1 CABLE 3 
C874 284 FIRE PR01339 JB298 PEE3 10AWG 1 CABLE 3 
CG1007 254 CUSTOME901 CUSTOME1 1/0AWG BARE CON4 
CG1008 333 PACKAGEI901 CUSTOME2 4/0AWG BARE CON4 
CG1031 230 JB019A TL901 CUSTOME1 1/0AWG BARE CON4 
CG1032 231 JB019B TL901 CUSTOME1 1/0AWG BARE CON4 
CG1033 233 JB020A TL901 CUSTOME1 1/0AWG BARE CON4 
CG1034 234 JB020B TL901 CUSTOME1 1/0AWG BARE CON4 
CG1038 381 JB021 A TL901 CUSTOME1 1/0AWG BARE CON4 
CG1051 280 GENERAT(901 CUSTOME2 4/0AWG BARE CON4 
CG1059 335 BUS DUCT901 CUSTOME2 4/0AWG BARE CON4 
CG902 157 TURBINE t901 CUSTOME2 4/0AWG BARE CON4 
CG906 182 MAIN TRAt901 CUSTOME2 4/0AWG BARE CON4 
CG907 146 METALCLt901 CUSTOME2 4/0AWG BARE CON4 
CG910 161 COOLING 1901 CUSTOME2 4/0AWG BARE CON4 
CG914 121 TURBINE E901 CUSTOME2 4/0AWG BARE CON4 
CG915 119 ACCESSOl901 CUSTOME2 4/0AWG BARE CON4 
CG920 134 GENERAT(901 CUSTOME2 4/0AWG BARE CON4 
CG926 171 GAS FUEL901 CUSTOME2 4/0AWG BARE CON4 
CG927 176 LUBE OIL [901 CUSTOME2 4/0AWG BARE CON4 
CG928 252 WATER W,901 CUSTOME2 4/0AWG BARE CON4 
CG929 172 AIR PROCI901 CUSTOME2 4/0AWG BARE CON4 
CG931 183 AUXILlAR'V901 CUSTOME2 4/0AWG BARE CON4 
CG933 201 LIMIT AMP901 CUSTOME2 4/0AWG BARE CON4 
CG954 158 GAS SCRU901 CUSTOME2 4/0AWG BARE CON4 
CG964 128 EXHAUST 901 CUSTOME2 4/0AWG BARE CON4 
CG965 129 EXHAUST 901 CUSTOME2 4/0AWG BARE CON4 
CG983 283 FIRE PR01901 CUSTOME2 4/0AWG BARE CON4 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:20 PM
blank)
ROL CABLES WITH "C" PREFIX CONTAIN A NOMINAL NUMBER OF SPARES. 


RE TO BE SUPPLIED BY OTHERS. 
S OF THE INNER EDGE OF ANY BEND SHALL NOT BE LESS THAN SHOWN IN TABLE. THIS RADIUS DOES N 
CH INTERFACE WITH GAS TURBINE SUPPLIED EQUIPMENT. 
NT. 


LOCATION OF CABLE DESTINATION POINTS lJB'S. ETC.l WITHIN EACH ON-BASE COMPARTMENT. 
N PROPER CONDUIT OR RACEWAY MATERIAL. SEE M.L. ITEM 0435. AND IN ACCORDANCE WITH LATEST 
E DIAGONALLY OPPOSED. 


PurDose SDecial Notes 
CONTROL SIGNALS 
INSTRUMENTATION SIGNALS 
FLAME DE 
FLAME DE 
125VDC SI15 
3 PH. SUPI15 
CONTROL SIGNALS 
INSTRUMENTATION SIGNALS RTDS 

~ERMOCOUPLES 

GAS DETE 
3 PH. SUPI15 
3 PH. SUPI15 
CONTROL 15 
INSTRUME 

~ERMOC 
~ERMOC 

CONTROL 
CONTROL 15 
3 PH. SUPI 
3 PH. SUPI 
3 PH. SUPPLY 23HG-1.-3.-5 
3 PH. SUPPLY 88TK-1 
3 PH. SUPPLY 88TK-2 

~ERMOC15 
~ERMOC15 

INSTRUMENTATION SIGNALS 
3 PH. SUPI15 
23BD 
VT SIGNAL 15 
KATO EXCITER 
INSTRUMENTATION SIGNALS 
3 PH. SUPI15 
PROXIMITI 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:17 PM
blank)
PROXIMITI15 

PROXIMITI15 

64F EXCIT15 

3 PH. SUPI15 

26HT-1.-3 
FIRE DETECTORS CIRCUIT (A 1 
FIRE DETECTORS CIRCUIT (B 1 

3 PH. SUPI15 
PROXIMITI15 
CONTROL 15 

3 PH. SUPPLY 23VS-1 

MOTOR HI15 

GAS DETE 
RTDS 88CR-1 

20TW DEVICES 

MOTOR HEATER 23TK-1 

63TK-1 

MOTOR HEATER 23TK-2 

63TK-2 

3 PH. SUPI 

MOTOR HI 

~ERMOC 

96CD-1A ~ 

AC LIGHTS 
DC STANDBY LIGHTING 

LIGHTS -RECEPTACLES 

CURRENT15 

CURRENT15 

CURRENT TRANSFORMERS 24-26 

CURRENT15 

CURRENT15 

CURRENT15 

125VDC B15 

23HG-20 15 

3 PH. SUPI 

120VAC Sl 

CONTROL 

LIGHTS. 2E 15 

~ERMOCOUPLES FTG-1 A.-1 B.-2A.-2B 

480V TO C11 

480V UNIT LIGHTING 

480V SITE LIGHTING 

480V CEM LOADS 

480V ALTE13 

480V NORI12 

480V WELDING OUTLETS 

125VDC TC12 

125VDC TC13 

125VDC H:12 

125VDC H:13 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:14 PM
blank)
480V SUPPLY TO GAS HEATER CONTROL PANEL 

~ERMOCOUPLES 

GAS FUEL HEATER EMERGENCY STOP 
FUEL GAS HEATER CONTROLLS 

480V SUPPLY TO AUX TRANS 

CT'S 7-9 & 11 

CT'S 27-29. 48-50 SIGNALS GCP UNIT #2 TO GCP UNIT #1 

CUSTOME13 

CUSTOME12 
EVEN UNIT TO ODD UINT CONTACTS 

ODD UNIT TO EVEN UINT CONTACTS 
EVEN UNIT TO ODD UINT CONTACTS 
ODD UNIT TO EVEN UINT CONTACTS 
ODD UNIT TO EVEN UNIT CONTACTS 
EVEN UNIT TO ODD UNIT CONTACTS 

96GR-1. 96AW-1. 96GG-2. 96GV-1 

96GG*2 

52G FAN ALARMS 

39V-3A 15 

39V-3B 15 

CONTROL SIGNALS 

~-ID-1 THERMOCOUPLE 

~-ID-2 THERMOCOUPLE 

~-ID-3 THERMOCOUPLE 

1201240VAC SUPPLY 

20TH-1 

33TH-3 

96TH-1 

65EP-3 

96BH-1 

96BH-2 

CONTROL SIGNALS 

CONTROL SIGNALS 

3 PH. SUPPLY 88FC-1 

3 PH. SUPPLY 88FC-2 

3 PH. SUPPLY 88FC-3 

3 PH. SUPPLY 88WC-1 

3 PH. SUPPLY 88WC-2 

MOTOR HEATERS 

METERING 

METERING 
DIGITAL CONTROL SIGNALS OUT 
DIGITAL CONTROL SIGNALS OUT 
DIGITAL CONTROL SIGNALS OUT 
DIGITAL CONTROL SIGNALS OUT 
DIGITAL CONTROL SIGNALS IN 
DIGITAL CONTROL SIGNALS IN 
DIGITAL OUTPUTS TO CUSTOMER ALARM PANEL 

ANALOGS IN/OUT 

ANALOGS IN/OUT 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:11 PM
blank)
REMOTE EMERGENCY TRIP R5E 
3 PH. SUPPLY 88CR-1 
3PH. 800 AMP SUPPLY FEEDER MCC1-AC 
3PH. 800 AMP SUPPLY FEEDER MCC2-AC 
CONTROL SIGNALS 
CURRENT TRANSFORMERS 51TN-2 
CURRENT TRANSFORMERS 50/51AT-2 
125VDC CONTROL POWER 
MEDIUM VOLTAGE SUPPLY 
96TD-1 
120VAC SUPPLY 96TD-1 
AUX 86G1 CONTACTS TO CUSTOMER 
AUX 86G2 CONTACTS TO CUSTOMER 
AUX 86RE CONTACTS TO CUSTOMER 
AUX 86AT CONTACTS TO CUSTOMER 
AUX 86BF CONTACTS TO CUSTOMER 
AUX 86G-1 CONTACTS TO CUSTOMER 
AUX 86G-2 CONTACTS TO CUSTOMER 
AUX 86BF CONTACTS TO CUSTOMER 
AUX 86RE CONTACTS TO CUSTOMER 
86T1 CONTACTS TO CUSTOMER 
AUX 86T-1 CONTACTS TO CUSTOMER 
86AT CONTACTS TO CUSTOMER 
CUSTOMER INTERLOCKS 
CUSTOMER INTERLOCKS 
CUSTOMER TRIPS AND PERMISSIVES 
CUSTOMER TRIPS 
96FM-1A 
CONTROL 11 
CONTROL SIGNALS UNIT #1 
CONTROL SIGNALS UNIT #1 
CONTROL SIGNALS UNIT #1 
3 PH. 480V11 
63QV-1 
3 PH. SUPPLY 88QV-1 
MOTOR HEATER 23QV-2 
5 TWO WIRE TRANSDUCER PACKAGE 
CONTROL POWER SUPPLY 
63AD-4 
59CM RELAY 
13.8KV TO TRANSFORMER PRIMARY 
13.8KV TO TRANSFORMER PRIMARY 
CONTROL SIGNALS 
120VAC SUPPLY 34GF-1 
3 PH. SUPI 
MOTOR HI 
3 PH. SUPI 
MOTOR HI 
71 GS-1.-2A.-2B.-2C 
23LC HEATER 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:08 PM
blank)
CONTROL SIGNALS 

120VAC SUPPLY 

CONTROL SIGNALS 

POWER SUPPLY 230 VAC 88RC-1A 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND (11 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 

GROUND GRID CABLE 


(Stamp comment
#41 dborgstadt
12/19/2010 12:54:05 PM
blank)
OT INCLUDE PULLING TENSION CALCULATION. SEE M.L. ITEM 0435 FOR FURTHER DEFINITION. 

ELECTRICAL CODES. 


